Forum / A-C, Heat Pumps & Refrigeration / Converting Knots to CFM
• Post a Reply to this Thread

## Converting Knots to CFM (11 Posts)

• ### Turbometer Usage

I want to measure CFM from each of our poorly installed high velocity air conditioning system's 2" dia. supply outlets and then compare the aggregate CFM to the air handler's rated CFM. The purpose is to detect leakage / inadequate airflow. I purchased a TurboMeter, an electronic wind speed indicator made by Davis Instruments. It can read wind speed in knots which is equal to FPM x 100. How do I convert knots to CFM? I know that the TurboMeter is what high velocity AC firms use for this purpose. Please note that I am a homeowner and not a contractor.
• ### Knots to CFM

How about furlongs per fortnight. Cross sectional area of the duct in square feet times average velocity in feet per minute=CFM.

• ### S Ebels...

I have seen that to where the trunk line is really short. Especially with unico, they would rather you run more trunk line as close to termination as possible. 10' @ 40 cfm per outlet and 10% reduction for every 5' over 10'. My .02 Mike T.
• ### W.C.

WC is inches of water column. It's an accurate way to measure small pressures. 27.72 inches of water column equals one pound per square inch. The 1.0 to 1.8 inches WC is a pressure inside the duct not the line set.
• ### 1.0 to 1.8\" WC

Thanks to those who explained that knots x outlet area in s.f. = CFM. What does a WC figure actually represent in layman's terms? Pressure? What would be the reasons for an unacceptable reading if correct dia. tubing was used for line sets?
• ### Knots to CFM

For all round outlets multiply knots by 2 to obtain cfm. For the slotted outlet multiply reading by 4 then add 4 to get CFM. Example: round outlets with knots reading 16.3 has 32.6 CFM. Normal range is between 20 and 40 CFM. Slotted outlets with 7.1 knots has 32.4 CFM. Normal range is between 15 and 35 CFM. There is a meter similar to what you have that will automatically convert this for you. Hope this helped. One additional thought,..before you even check these check the external static pressure in the supply plenum,...should be around 1.5" of water. Mike T.
• ### Wow

Did I read that right 1 to 5 inches?No wonder they only need one return.
• ### Sorry don,......;-)

Was early in the morning and eyes and fingers weren't working yet....;-) I corrected it just for you... Actually it's 1.8" max and no less than 1.0". Recommended is 1.5" wc Mike T.
• ### i knew that.

Just messing with ya.Good Morning!
•