but we have used on quite a few projects.... utilized dual supply piping and saw good results. Used in one great room where wall space was extremely limited due to glass and got expected results. Also have used on low temp radiant systems where baseboard was requested. Nice product albeit a little pricey.
Since I last posted on the wall the board rep. came out for the second time to look at the job , but this time he had some new numbers as to what the board will put out . It is about 55% of what the original numbers were . Wish I would have known that before I did a whole house with that stuff. I am in it up to my you know what now !
Rob the new numbers are 345 BTU/ft @ 110 deg average water temp. The old numbers were 535 BTU/ ft @ 110 entering water temp.
They are stepping up though and are going to help me fix the problem , thank God .