This thread has been bookmarked. Visit your bookmarked threads to review.
Post a Reply to this Thread
system bangs (6 Posts)
system bangsliving in house for 12 years,have a single pipe system that never banged queit as a mouset.Recently my pressuretroll failed system went to 25psi before the air valves screamed and I shut down system. Replaced pressuretroll set @2psi now system bangs???Help anyone Thanks
Water got places it shouldn'tAt that kind of pressure you probably had water in all kinds of strange places and it's banging because some of that water is still there.
Can you localize the hammer to an area? Check all the piping you can get to 9use a level, don't trust your eye) and make sure it's all got the correct slope and make sure there aren't any sags (run a string along each run to check for sags).
BobSmith G8-3 with EZ Gas @76,700 BTU, Single pipe steam
Vaporstat with a 12oz cut-out and 4oz cut-in
And I might addwhen you get done doing what Bob suggested, which is exactly correct, check those air valves and any traps. 25 psi may well have damaged them pretty badly.Jamie
Building superintendent/caretaker, 7200 sq. ft. historic house museum with dependencies in New England.
Hoffman Equipped System (all original except boiler), Weil-McClain 580, 2.75 gph Carlin, Vapourstat 0.5 -- 6.0 ounces per square inch
Gauge glassHow does the water in the gauge glass look? Is the water level fairly stable while running? Does it drop a lot during a heating cycle and then return shortly after the system shuts down?Weil-McLain EG-45 connected to 392sqft of radiation via two 2" risers into a 3" drop header and 2" equalizer. Using Rectorseal Steamaster water treatment to greatly reduce corrosion in the boiler.
Steam system pictures updated 6/5/14.
system bangsI had a similar issue where I had abnormally high pressure during a cycle because of a pressuretrol fail. Needed to replace a valve, repack another, and completely get rid of all my rad vents. I stlll swear my system makes more noise than before, but I was waiting for the winter to end before I start tinkering.
system bangsHey guys thanks for all the suggestions replaced air valves and had no banging this morning.On one radiator I had to go with a slower valve and it stopped the bang. Once again thanks to all for your help