replacement relay which replaces the L8148E. The L8148E has a 24 volt burner circuit. As long as your gas valve is 24 volts then you can replace the "J" with the "E". I am assuming the "E" is a new control and not one that was used previously? If your system is a powerpile system the "E" will not work.