This thread has been bookmarked. Visit your bookmarked threads to review.
Post a Reply to this Thread
steam pipe size (6 Posts)
steam pipe sizeI have just bought a new ( old) building with steam heat. One of the rooms was an addition over an old porch and did not have a radiator in it. I had a plumber install a new radiator in the room and hook up the pipe in the basement . They installed 3/4 inch to the new radiator, around a 10 ft run with three 90 degree elbows. but all the other ones in the house are 1- 1/4 inch pipe. Except a base board radiator in one room with 2 pipes ( all the other radiators in the house are one pipe. The new radiator won't heat up all the way across the fins only three closest to the intake heat up and the heat won't go all the way across the radiator. I have a new Hoffman adjustable vent on it and and have tried all the different settings. Question is the 3/4 pipe to low of a volume to work with my radiator?
That 3/4" pipeis small for normal steam use on a one pipe radiator, make sure all the new piping is properly sloped back to the steam main. Also how big (height, number of sections, and columns per section) is this radiator - post a picture of the radiator.
BobSmith G8-3 with EZ Gas @ 84,200 BTU, Single pipe steam
Vaporstat with a 12oz cut-out and 4oz cut-in
interesting thing about pipe sizingin that in my research, i've come across many different charts, and they dont agree..i bet they all worked for the engineer though..here is the catch, if one guys chart says you can use a 1'' pipe, and another guys chart says it should be 1 1/2'', you can only follow the charts if your doing the whole system..otherwise you had better get out and look at whats already there, as you don't want to increase or decrease the path of least resistance..or you will increase or decrease the result too! Did that make sence? In an existing structure what someones chart says, means less than following suit with whats there. Also, if the other rads are 1.25'' and only have a couple elbows in the runouts and they are short, you will need to upsize that horizontal portion of the runout to compensate for the extra elbows.Serving Cleveland's eastern suburbs from Cleveland Heights down to Cuyahoga Falls.
thanks for responseI will take pics of the radiator and pipes on run today and post tonight
Gerry's rightit has to match the rest of the system. That plumber needs to replace the pipe with one of the proper size- at his expense, not yours."Reducing our country's energy consumption, one system at a time"
Steam, Vapor & Hot-Water Heating Specialists
Oil & Gas Burner Service
Baltimore, MD (USA) and consulting anywhere.
SteamLet me guess...it was done in copper, too?- Joe Starosielec
Guaranteed performance. Guaranteed energy savings.
Serving all of NJ, NYC, Southern NY State, and eastern PA.