Forum / Radiant Heating / Three port thermostatic mixiing valves

## Three port thermostatic mixiing valves (4 Posts)

• ### Three port thermostatic mixiing valves

Hi

When you look up the Cv of a three port TMV, is the pressure drop and flow based on flow from one inlet to the outlet or both inlets to the outlet, or does it not really matter. I am thinking about the circuit where a TMV is used for boiler protection - the biggest pressure drop is likely to be across the TMV, but I can't get my head around if it makes a difference if one or both ports are open?

Also, we use metrics in NZ but most Cv's I have seen are based on imperial measures - are there conversion factors to convert Cv's or do you just have to develop your own?

Thanks.

Regards,

Santilal
• ### The metric flow factor unit is Kv

Kv would be cubic meters per hour (m3/hr.) of a 16• c water with a 1 bar pressure drop.

Cv is GPM of 60•F water with a 1 psi pressure drop

Kv = 0.862 x Cv

The thermostatic valves built for boiler protection have larger flow rates and are usually a fixed temperature cartridge.

The pressure drop either Cv or Kv is the flow thru the valve to the outlet.

Keep in mind a valve with a Cv of 3 can flow more then 3 gpm, but you will have additional pressure drop.

Here is a little spreadsheet we use to calculate flow, pressure drop, and gpm. I'll see if we have one in metric units if you would like.
• ### Thanks

Hi

Thanks for that. From your answer it appears that the Cv is not dependent on either or both hot and cold ports being open or closed.

Cheers.

Santilal
• ### correct

what comes out of the mixed port is the blend of the H &C port. If it needs more hot, that port opens as the cold closes down. The wax cartridge inside move the spool up and down to vary then opening into the valve from the H & C
•