Hello to all.
I recently changed a blower motor (1/3 hp) that uses a belt to drive the blower on an old 3 ton air handler that customer states had started to make squeeking type of noises before it died. I replaced the motor and belt and about three weeks later it was making a constant high pitch noise worse than before, not sure where its coming from. I adjusted the pully on the motor to be more in line with the pully of the blower and for the remainder of the time I was there it was fine but it started again soon after that. Now it starts with a constant cycle of humming and then squeeking and again humming then squeeking.
Other important things I noticed are
1)If I remember correctly when I removed the cover the noise stopped
2) The new belt after 3 weeks seemed to have been a lot looser then when first installed.
3)Noise only happens with belt in place
4) blower has pillow type bearings that seem to be properly greased.
Any help would be greatly appreciated, Michael
Remove the belt, grab the(driven) sheave and shake it up/down/sideways/back/forth.Do the same for the motor. Do you feel any movement, hear any clunk ,clunk noise? Is the pillow block bearing a one piece bearing or is it a babbit type( take apartable)? Grease or oil in the bearings? A belt that loosened up in a few weeks is not right, possibly it was over tight, wore out the bearing and streached the belt out a little?
This post was edited by an admin on September 4, 2013 5:18 AM.