This thread has been bookmarked. Visit your bookmarked threads to review.
Post a Reply to this Thread
Too much to list (9 Posts)
Too much to listNot sure what they were thinking
I don't know where to start
2 in header?
Bullheaded tee,no swing joint
16 in. A Dimension
Level mains and back pitched drip returns
Main air vents 27" above waterline, above boiler
Plugged pigtail & 3/4 90 for presuretrol
Hartford loop close nipple 2 " above waterline
Auto feeder wired wrong not working
boilerLooks like that boiler should be in a pit.
SteamThis is why drop-headers were invented. But, then again, knuckleheads think a dropped header is just a way to get a bruised toe.- Joe Starosielec
Guaranteed performance. Guaranteed energy savings.
Serving all of NJ, NYC, Southern NY State, and eastern PA.
drop headerA drop header wouldnt work there, He said there is 16 in of a dimention. It needs to be in a pit or needs a condesate pump.
Header and pumpIn my opinion it needs a drop header and a condensate pump.Weil-McLain EG-45 connected to 392sqft of radiation via two 2" risers into a 3" drop header and 2" equalizer. Using Rectorseal Steamaster water treatment to greatly reduce corrosion in the boiler.
Hartford Loop?It looks like a completely dry return to me. Probably not a good idea with that A dimension. It probably calls for water mid-cycle, so add "fluctuating water line" to the list of troubles.
I'm not sure how you measured that A dimension. Is that from the max water line to the header? If there's more than 28" from the water line to the main a drop header should work.1983(?) Peerless G-561-W-S
3" drop header, CG400-1090, VXT-24
A dimensionI measured A dimension from where the
Feeder satisfies the lwco.
At that point it was 2 in below Hartford loop
It was a toss up weather to raise up above
Close nipple or get as much distance as possible.
I would like to pipe the drip down into a wet return and then back to the boiler
Customer doesn't want to do any work yet ???
Bad installWhat were the symptoms which led to the service call?--NBC
Check heatCheck heat for the season