This thread has been bookmarked. Visit your bookmarked threads to review.
Post a Reply to this Thread
2 Gallon electric water heater. (13 Posts)
2 Gallon electric water heater.Please see attached pictures, this is a 2 gallon electric water heater used instead of a boiler and is only serving 1 towel rail in an apartment building. I did not do the install, but he is having problems with air. I have been back a couple of times and removed the air, but the problem seems to keep reoccurring - I am thinking of adding 1 small spirovent or equivalent air eliminator and bring the make up water and expansion tank in at the bottom of the spirovent.
This may seem simple, but I have never seen a 2 gallon electric water heater used instead of a boiler before. Anyone see any problems with this?
Thanks in advance.
Seems like....a lot of work. An electric towel warmer would have been a simpler approach. I would add a hy-vent where the PRV is and add a 1/2 cup of dawn dishwasher detergent. 99% chance that works.... Fix is from Mark Eatherton.This post was edited by an admin on September 23, 2013 5:14 PM.
OK...I agree with above, an electric warmer would have been cheaper and easier.
simple question.... which was is the heater installed? the correct way? and your picture is sideways or.... is the heater laying on it's side?
If the heater is on it's side... your never going to get the air out, it's trapped in the heater... big ol air pocket, reinstall the heater the way it was intended and you fix your problem.This post was edited by an admin on September 23, 2013 7:14 PM.
If that towel warmer is installed sidewaysit must be holding some kind of quadrature gravity towel.
ThanksTowel rail is over a bathtub he did not want to use electric
I am not Familiar with hy-vent
It is installed correctly picture is Sideways
You can just see the bathtub in the pictureThis post was edited by an admin on September 23, 2013 7:23 PM.
a Hy-vent...or a float vent. http://www.taco-hvac.com/products.html?current_category=87
I didA temporary hook up with a 4.5 gal ariston electric water heater, and a Laing circ with a built in thermostat for about 400sf of RFH . Between the differential on the water heater, and the differential on the thermostat for the circ 'twas not the best control, but temporary.
Battled air also., and the aqua stat on the water heater would run wild sometimes.
Electricity was killer on the wallet.This post was edited by an admin on September 23, 2013 9:46 PM.
Electric Towel Warmer:Nice install, bad idea.
As far as electric towel warmers, that's what GFCI's are for.
There should be GFCI's in the bathroom. If you take a power cord, plugged into a GFCI protected outlet, get into the tub full of water, and stick the live end of the cord into the water, the circuit will trip before the electricity can "get" you.
Too bad that someone who should have known what's up, didn't know.
If that water heater...... has an anode in it, there will be gas formed and there doesn't seem to be a way for it to escape. I'd agree with venting at a point where the gas collects.... unless the "quadrature gravity" is at work. :~o
I agree...I agree with Chris on the electric. I put in the electric version of
that exact warmer. They literally screwed the element in where the
piping threads in and filled the thing most of the way with water (a
little air for expansion).It was right next to a shower with the timer installed across the room. It worked great. Some people fear electricity
and there is no talking them out of it. Personally, I fear all that extra stuff in cabinet waiting to spring a leak and flood my house.
I had not thought of the anode. An air vent is a good call,
Towel WarmerHi guys, Installed the vents as suggested, still having the same problem. I did try adding dish soap. Customer claims it worked for 3 weeks and that's it. I'm wondering if I install a 3/4 inline spiro vent like I do on all the larger systems, if this would solve the problem? Any advice is greatly appreciated. I fully understand that an electric towel warmer would have been easier, cheaper, and a better option, but the owner really wants to stay with this. he wants to get it fixed, so swapping it out for an electric towel warmer is not an option. (towel warmer picture is sideways)This post was edited by an admin on June 30, 2014 11:50 AM.
Expansion tankI think the expansion tank is on wrong side of the pump, pump away from exp. tank.
Air seperator would definitely help. I like to stay with the taco 4900 residential.
Also I would get rid of the pressure reducer.
I lust took second look expansion tank Looks good. ( pumping away)
I would put the air seperater where the tank is and set it up like a boiler.
vertical air purgerA vertical air purger would be ideal, and add a hygroscopic vent on the towel bar if there is a connection.
Could be that small circ is not providing the 2 fps to get all the air back to the vents? Save those vents for high point applications, they are not a replacement for an air separator.
Maybe pull the circ and be sure that the impeller spins and is not partially plugger and not providing enough flow, it's about the only thing that may have changed.