once again a quick response and great techncial assitance from Jim Sokolovic the guy in the Lab who is always a big help.
Thanks for the response Steve.
Will call tomorrow and get the change out for this obsolete and defective Integrated control.
with a RAM Model H1MC5-01 Integrated Control Board. Does anyone have specific information on this board and its operation.
Followed the exact procedure for setting up system as outlined in Slant/Fin instructions everything checks out. Getting intermittent operation on the board. I want a procedure for checking the electronics on the board. I have these for Honeywell and United Technology boards but not this board. I am getting two different microamp readings depending on direct from flame sensor or from flame current jack. I am reading 15 microamps at jack, 5 microamps at sensor???
No one locally has this board.