Charlie from wmass
Joined on September 21, 2006
Last Post on December 9, 2013
@ November 5, 2008 7:30 PM in Burner stops when tank reaches 100 gallonsThanks Mark for you reasoning behind your choice. You should remember that a gas unit should be maintained even though they seldom are. I find a once over each year can prevent a small issue from being a big one, such as a dripping flange causing a premature failure of a circulator, or a worn expansion tank causing issues with the rest of the system. As for finding Reiello tachs in MA I do not know of many companies out here in Berkshire county who do not have several guys who are well trained with them and also parts are availlible in every wholesaler in the county. I often see gas or oil is more then just dollars and cents. I seems tech support is more of an issue to many people.
@ November 3, 2008 10:46 PM in sheeeese...Gee can't you just use an electric instant water heater and save that nasty gas bill??? (sarcastic answer btw) Amazing what passes as a heating system. Kind of jaded today spent it repairing scorched air systems.
@ November 3, 2008 10:36 PM in Burner stops when tank reaches 100 gallonsOk since I install both systems and I do use an analyzer for both fuels I do not agree fully with the last 2 posts. I find a well maintained boiler does not have many break downs. I was under the understanding that oil had 40% more heat per unit. I also was under the understanding that the carbon footprint of such a change over would negate any reduction sought from gas. As for flower beds as a gardener I can plan around an occassional oil delivery and good suppliers are careful when they do deliver. I am not trying to talk people out of providing work I simply do not understand the math. Is there not also a shortage of natural gas that is supplemented with propane? Propane being the product of the same crude oil that the fuel oil comes from. As for the use of the last of the oil in the tank have you tested for a leak in the suction line?
@ November 3, 2008 6:59 PM in Burner stops when tank reaches 100 gallonsjust wondering why go gas if you have a buderus with a reiello? AFUE drops when firing gas in oil boils far as I knew, am I wrong? I can see it being a thought when you have an old boiler and rebates are taken in to the mix.
@ November 2, 2008 10:18 AM in Does the low water test make my system less efficient?Can you send a few pics of the near boiler piping and the return lines?
@ October 29, 2008 10:46 AM in CRACKED cast iron pipeThey may have been cracked from the day they went in and just with wear are showing a leak. When the old timers of less than high standards cracked a piece when cutting it they often just grabbed the asphalt paint and covered up hairline cracks. Even then they had hacks.
@ October 29, 2008 10:42 AM in Burnam Mega Steam won't shut offCheck for micro switches on the t stat. I am not familiar with the one you used but the honey well digital round t stat has 3 switches that need adjusted for steam systems.
@ October 28, 2008 1:26 PM in New Twist on HeatingHelp?Windows are said to be the least effective return for your money of any up grade. Insulation depends on what you add and how many R's you can increase the system. A new boiler starts saving the first day it fires and with a proper installation has the fastes return if you system is as old as a 1950's model. Just my 2 cents. Have fun with the new baby mine are 5 and 8 now and it is a fun and wild ride.
@ October 27, 2008 11:00 PM in I smell gas...yep from the description and the pic it is clear who had the gasket issue. At least they seem to stand behind te stainless steel boilers they have sold under another color of jacket. There was a recall on their condensate wye fitting but they sent me the parts and a check to defer some of the cost of changing the parts. I will check them as I install thanks for the heads up.
@ October 22, 2008 4:15 PM in Who make the most fuel efficiency steam boiler?I thing in gass they are the most efficient due to their wet base design, but with the power burner they can not run without electricity as some of the old steam units with powerpiles could. I can not find the actual A.F.U.E. ratings for them when fired on gas. Does anyone have the ratings?
@ October 9, 2008 1:44 PM in Lack of heat questionStarch is right that is a boiler feed pressure regulator. job must be near me if it is that goofy. I wonder if they have one feeding the boiler? Any pics of the boiler piping?
@ October 6, 2008 9:32 PM in good day to be a plumberOk stopped by the holey water spout today. Turns out the wter pressure has been low for the whole house for years. Funny how now it is an issue. They have over 50 pounds pressure when the faucets are running. Could be the 3/4" compression stop on the main and the fact the main runs 60 feet to the street and it is 3/4" up to the first bathroom, now 2 and a half bathrooms in the house from the original one bathroom. no mention of water pressure before I started the work though or until I went there today.
@ October 6, 2008 9:06 PM in GB145 and Cast Iron RadiatorsYou need a heat exchanger with the aluminum block boilers or the iron in solution can clog the water passages. Other wise no issues. This goes for lots of iron in the manifolds or loops also. Also electrolosis. The high mass of the system and hopefully over sized rads should make for lower water temps for heating the house, which would be to the benefit of the Buderus. I could not find it in the current manuel maybe the WeilMcLain I am thinking of but I would say that the sludge and other goodies is the only thing to worry about. Maybe a good dirt seperator would also help. If all else fails check with buderus direct they have good people there from my experiance with them.
@ October 6, 2008 9:04 PM in GB145 and Cast Iron RadiatorsYou need a heat exchanger with the aluminum block boilers or the iron in solutin can clog the water passages. Other wise no issues. This goes for lots of iron in the manifolds or loops also. Also electrolosis
@ October 2, 2008 11:43 PM in good day to be a plumberThanks guys wonder sometimes if it is me, Glad at least a couple folks see the humor in these things.
@ October 2, 2008 6:37 PM in good day to be a plumberok Day started off wonderful. I had some service calls with new customers both of whom were happy to have a prompt and well spoken plumber who fixed what was ailing them and was on his way. Then I got home. It appears the remodel I did last month has an issue with their new tub and shower. So I call them back and ask what the issue is. They tell me the water coming out of the tub spout has a hole in the middle. I kid you not. They want to know what I can do to fix this. A little back ground, here in MA we can only install single handle pressure balance tub and shower faucets. It is also on the second floor and has 1/2" copper supplies. So guys how does one make 2 1/2" copper pipes fill a 1" tub spout?
@ September 29, 2008 9:33 PM in My father has passedFrom one son of tradesman to another You got my condolenses. Your Dad is actually younger than mine and this does make me think. The best to you and yours at this time. Remember it is the good things that need to be remembered and the living who need the consoling, those who have pasted are in the hands of someone else.
@ September 29, 2008 9:26 PM in Why Can't I Boil Water in an Oven?It is boiling. It is just not condensing to form vapor.nor is it trapping hot steam under hotwater as the oven has heated the whole tray not just the bottom of the pan. Steam is clear, Vapor is white.
@ September 29, 2008 10:53 AM in Older H.B. Smithyeah i know it is a hog just remembered the contest smith had for oldest working boiler and was wondering if i was even close in age.The bacharach digital combustion analyzer says 70%. but I know a lot of heat is just going everywhere but into the water.
@ September 27, 2008 3:36 PM in Older H.B. SmithHard to say how old the house is but found out today it used to have gas lights in it.
@ September 25, 2008 10:15 PM in Older H.B. SmithGirl friends mother has a boiler, I know never a good start to a story. Anyway it is a round H.B. Smith coal steam boiler converted to oil converted to gas. tester says it is firing 72% when steaming. I was just curious where I can look it up to see just how old it is? Yes it is slated to be changed but you know how these things go.
@ September 25, 2008 10:10 PM in One pipeI would also check the rating on that relief, does not look to be the right size, I would expect a bit bigger of a relief. I was wondering if the tees in 13 and 18 were plugged off where they had vents before? maybe out on 90's and nipples? And ditto to the other suggestions. Enjoy as it will feel nice when it is humming away in Febuary with no spitting.