Joined on February 3, 2007
Last Post on February 26, 2014
@ August 7, 2013 5:11 PM in Direct venting steam boiler?I have used Tjerlund in the past, they make a great product with excellent factory support
@ August 3, 2013 12:43 PM in high head pressuresTechman has the right idea, even though the cond. coil looks clean, washing out the coil with a hose and some coil cleaner will alot of times drop the head press. 15-25 psig, watch all that dirty water run out
@ July 30, 2013 9:09 PM in Leak sealOne way is to press test with nitrogen, check with liquid leak det. solution. Another way is to use a good electronic leak detector while unit still has a refig charge or add nitrogen with a refrig. tracer. There are dyes you can put into systems, I found they are messy and hard to get out of your guages,
@ July 30, 2013 3:12 PM in Leak sealHad a bad exp. used on a low temp Kramer hot gas defrost R 404 system , ended up with restrictions in system
@ July 26, 2013 5:34 PM in Fire Damaged Package Heat Pump UnitI would be concerned about any soldered connections on unit, most fires reach well over 1000 deg F. some solders have a melting point between 750 -1100 deg.F. Some carrier units had a fusible plug on the suction line set to blow if temp./press. got to high. There are several products to check condition of refrig. oil. also any residual smoke smell may be trapped in unit and duct insulation You should have a visual inspect. by a pro.
@ July 22, 2013 10:53 AM in low temp splitget all unit info 1rst a fan curve will help you determine air flow, chances are the cond unit also has ajustable air flow data available, you will need a good tachometer.
@ July 22, 2013 10:46 AM in circulators/pumpswater enters the center (eye) of the impeller from the suction side of the pump, on larger pumps with limited horizontal piping a suction diffuser is needed to direct water to the center. the centrifugal force created by the impeller imparts velocity to the water at the outlet of pump, creating a differential across pump. ( differential machine ) Its crucial that the suction press at pump does not go into a negative which will cause pump problems. I have additional info on reading pump curves if needed plus all that Jamie said
@ July 21, 2013 6:53 PM in low temp splitYou might want to do the detective work, make sure the units are the right size for the heat load in the bldg and are installed correctly before you spend to many unbillable hrs on the job, than get I.O.M.s and fan curves for units.
@ July 20, 2013 6:06 PM in low temp splitDucted condenser coils almost always cause above normal. press./temps.especially if they were added to the original install and are almost always dirty unless signs of cleaning are evident. I would recommend getting in and washing out the cond. coil with cal clean for a start, than looking at air flow issues. you may have to cut some access holes, always wash out coils starting from the side opposite the air flow. that low superheat reading sounds strange with your other readings, how are you measuring it.
@ July 20, 2013 12:32 PM in A question of design (circuit setters)That sounds like a tough one, can you make a detailed piping drawing. I worked on several changeover systems in the past and am familiar with the fan coil and mechanical room changeover process, Usually direct return systems would have circut setters on the fan coils.
@ July 18, 2013 10:27 AM in Blower pulley sizes ?Well I typed in this site and obviously I typed something wrong, just look up pulley sizing on yahoo or culver motor, sorry for the confusion
@ July 18, 2013 10:23 AM in Blower pulley sizes ?www.culvermotor.com/Engineering-Formulas/Pulley-and RPM
contact the unit manufact, and get a fan curve, which will assist you on the correct rpm for cfm needed.
@ July 10, 2013 2:31 PM in condensationAny time you are operating a DX or chillwater coil you will have some condensate if the unit is operating correctly and there is moisture present in the air stream, the higher the relative humidity the more condensate. check your cond. drain line and trap and flush them out if needed, make sure your trap and condensate piping are installed per unit recommendations.
@ July 9, 2013 11:35 AM in Desperately Need HelpThe United Ass. of plumbers and steamfitters has its national training center at Washtenaw college in Ann Arbor, check into contacting someone there.
@ July 4, 2013 4:02 PM in case grounded compressor?what setting is your meter on, I recommend getting a megohm meter and re checking. always check the elec circut. for loose wiring or burnt comp. contactor contacts before condeming compressor. if it is single phase it could be a bad capacitor. If your not getting contiuity to ground it may not be grounded
@ July 4, 2013 1:41 PM in carlyle o6e compressor failurere read all the past posts that were sent to you and follow all recommendations
@ June 29, 2013 12:08 AM in unloaderUnloaders dont regulate oil they are a capacity control look up suction cut off unloader or www.xpedio.carrier/idc/groups/public/documents/... sounds like you have an oil return problem which someone misdiagnosed, so they kept adding more oil. at this point i would recommend that you take a class on compressors at your carrier dealer and recheck the design of your system (piping sizes, unit sizing and air side design
@ June 28, 2013 9:27 AM in Bad TXV ?What type of refrig, walk in box or under counter, what temp are you trying to maintain, are the derfost heaters oper. what type control , low press. control or liquid line sol. valve, door gasket condition. has someone been leaving door open.
@ June 26, 2013 6:53 PM in how to evacuate a precharged unitI am concerned you are a tackling such a large job with what I think your saying is no field exp. for your safety and others have a journeyman show you the proper procedure
@ June 26, 2013 3:21 PM in Condenser Fan QuestionI am assuming the unit is in cooling. i would wire the motor for high speed, check that your motor amps dont exceed rated amps, check rotation. freezing of suction line outside unit and at compressor would indicate other problems, possibly air side issues
@ June 25, 2013 6:21 PM in Condenser Fan QuestionIt all goes back to the size of cond. fan blade, a larger diameter blade would require a larger horsepower motor, the 2 speeds should indicate 2 different rpm's, say 825 and 1050, a larger horsepower motor can take the place of a smaller motor as long as the wiring and etc is big enough, check the rotation on the motor and motor amps, remember air flow restriction (dirty cond. coil ) on a propeller blade will increase motor amps, can you provide all motor data and a picture
@ June 24, 2013 4:46 PM in Add Boiler Feed Tank Or Not?looks like this si a hydronic compression tank, check with the local city boiler inspector,they may require a tank made of schedule 40 carbon steel