Joined on August 28, 2007
Last Post on February 10, 2014
@ October 4, 2013 5:34 PM in Buderus Logamatic worth it on new gas boiler? Compare vs programmable thermostats?is the price of comfort worth?
@ September 20, 2013 7:59 PM in Iron Piping near boiler on High effieciencywith a Vitodens, it's more work than propress that's for sure.
Black pipe flows more than it's equivalent size in copper.
@ September 6, 2013 4:53 PM in Contractor Recommendation in Long IslandMyself
@ August 24, 2013 6:39 PM in Instantaneous vs IndirectHow about your take on that paper Chris, I have some beer to drink and don't have time! :')
@ August 21, 2013 10:38 PM in Need a new oil boilerthe heatloss numbers on that 1600 sq ft. ?
my 2000 sq. ft. runs around 40,000 btu's / hr, fyi.
@ August 12, 2013 11:48 AM in Please Judge my layout...TT shows the boiler circ on the supply in the manual. Also your pumping through the boiler circ with the indirect circ in. Moving the boiler circ to the supply solves that issue.
@ July 31, 2013 8:28 PM in help with updating heating systemA Vitodens 100-26, but a Triangle Tube Solo 60 might be good too!
@ July 31, 2013 7:16 PM in help with updating heating systemMr. O'Brien is WHY??? you'd only install those mod cons in your own home?
@ July 29, 2013 7:12 PM in Expansion TankThe north shore has higher water pressure which has presented a problem sometimes. I recommend the DHW expansion tank and some manufacturers require it for the warranty to be in effect. Just my two cents.
@ June 28, 2013 11:37 PM in You like cars?looks like a Buick Regal in the background. Nice Cutlass!
@ June 23, 2013 9:13 PM in High vs Low efficiency gas boiler?Big boiler vs. small boiler. Smallest you can get should do it, with the appropriate sized indirect of course. Just my two cents.
@ June 22, 2013 10:05 PM in Fingerprints on Vitodens Cabinetif your having a tough time with the tire tracks.
Say that three times fast!!!
@ June 19, 2013 6:19 PM in DumbI've walked out of a store because the checkout line was too long.
Sometime's I don't even make it inside because of the capacity of the parking lot or lack thereof.
@ June 15, 2013 5:38 PM in High Efficieny Gas Boiler Recommendationhouse on Long Island, heat loss is probably around 100,000 btu/hr on a design day. FYI
@ June 4, 2013 8:33 PM in Delta-P/Delta-T Part #5is the boiler that can meet the demand of 3/8" pipe.
Can we make one small enough?
@ May 24, 2013 7:25 PM in I have noticed more and more shotty workbefore you get to the job. 1 day and I hadn't been there before and all I had to work off of was the before photo and a couple of dimensions.
@ May 23, 2013 7:41 PM in Opinions Wanted!!saved a buck or two by getting the G115WS/3.
Did you get ODR?