Joined on November 24, 2007
Last Post on July 24, 2014
@ March 10, 2011 12:58 PM in Hammering on boiler shutdownwhat sort of vent do you have on this radiator?
are you sure it is water-hammer, and not the sound of expanding/contracting metal rubbing against a wood joist?
how do you know that your pressure is really following the settings of the pressuretrol?
is this riser closest to the boiler, off the main?--nbc
@ March 10, 2011 12:03 AM in Can you resell or donate a used boiler?http://www.heatinghelp.com/forum-thread/135547/Thoughts-on-steam-systems-opitions
perhaps the boiler could be downfired.
could it be resold to the installing plumber?
a donation of such a heavy item would be difficult.--nbc
@ March 9, 2011 11:55 PM in Can steam heat piping be replaced?can you post some pictures of the boiler, and from that we could tell if it is steam, or hot water.
there are some excellent mini-split heat-pumps-a/c's, and they do a very good job. they are not cheap, but will last a long time. have you asked a professional from the "find a contractor" button above. remember, that anyone you consult, especially if you have steam, must be a steam/hydronics professional. a mere hvac guy, or plummmmmer is not going to do the best job for you.--nbc
@ March 9, 2011 11:46 PM in Time Sensitive Question About Vaporstat mounting locationtry to get those operating pressures down to the ounces range, and see what the difference is.--nbc
@ March 9, 2011 5:53 PM in Time Sensitive Question About Vaporstat mounting locationclammy, he has the mod-u-pac, i mentioned to you: with 3 stages of firing:50%, 75%, and 100%--nbc
@ March 9, 2011 12:01 PM in Boiler pipes venting - elevate or notthe base of the gortons are made of brass, so you will be ok with screwing into iron or copper.
i put mine on top of some brass ball valves, for later ease of cleaning. use some teflon tape on the threads to enable their later removal, and don't put too much torque on the body, only use the lower flats for tightening!--nbc
@ March 9, 2011 11:54 AM in Thoughts on steam systems opitionsi would certainly not advise anyone to change over without a complete re pipe, but as a cost comparison, it might make it easier for the home-owner to see the cost of clammy's steam corrections in a more favorable light.
if you give someone the choice of spending $x to repair what is there, or $4x to convert to hot water [both using the same boiler], then the lower price of the steam repair is easier to bear. [hope i explained my thoughts clearly]--nbc
@ March 9, 2011 11:43 AM in Emergency steamer replacementcan you please elaborate on the "V5055/V4062 setup" for the 211 a?--nbc
@ March 9, 2011 10:09 AM in Thoughts on steam systems opitionswhat symptoms were there which prompted them to call you in in the first place?
are there all convectors in this house, or is it a mixed system, with some cast-iron radiators? could this radiation mix have contributed to some of the original symptoms?
will they contemplate an addition to the house sometime in the next few years?
can this system make some hot water for them, to use up some of the excess heating capacity?
can you compare the cost of re-piping/down-firing with running all new pex and hot-water rads/convectors for a hot water system, using the same boiler?
just thinking out loud.--nbc
@ March 8, 2011 1:27 AM in Boiler pipes venting - elevate or notthat vent should be protected by a menorah or antler, whose right angles will slow down any violent movements of water in the pipes. the danger to any main vent is damage caused by slugs of hammered water hitting them in their bottoms, which like any bottoms need protection.
it looks as though you need a newer, and bigger vent on that dry return, and any other dry returns in the system [is there one more?].--nbc
@ March 8, 2011 12:51 AM in Emergency steamer replacementnice job, but where is the skimming port?
and where is our favotite wika low pressure gauge?--nbc
@ March 8, 2011 12:46 AM in HELP! Automatic feed sounds like a freight train!how often is this happening, as there should not be such a great loss of water as to make this a daily occurrence
that sound is obviously coming from a chattering valve in the auto/over-fill. go to the website of the manufacturer [maybe mcdonell-miller], and you will find out if a rebuild kit is available. unless you are very handy, it might be time to call a pro, or wait until spring.
you may be able to moderate the problem by closing off the supply valve to the unit, and only opening it when you go down to check the boiler every couple of days [you do check the boiler regularly don't you?].--nbc
@ March 7, 2011 7:27 PM in Unbalanced heat distributionit is hard to diagnose this from a distance, but i'll gather some information.
1.is this hot-water or steam? if steam, is it 1-pipe or 2-pipe?
2.has the system always been so unbalanced? if not, was there something done to the system which preceded the imbalance?
3.what sort of thermostat is now in use [make/model]?
obviously, the system when first installed, would not have had these problems, so the goal is to bring it back to its previous state of operation.--nbc
@ March 7, 2011 6:33 PM in Pipes banging no matter what I dothe removal of one [presumably] small radiator should not cause water-hammer to suddenly begin.
when were the valves/vents replaced? were these the main vents? if they were the radiator vents, did you replace with the same type? if the radiator vents are too aggressive, and the main vents are inoperative, or under-sized, then the imbalance thus created can allow water-hammer.
if during the work, the boiler water became contaminated with a bit of thread-cutting oil, then the waterline might become unsteady enough for the hammer to start, or if the boiler became over full. perhaps that radiator was holding a section of the main steam-line piping up straight, and without it being now connected the line is sagging causing a pool of condensate to be trapped in the way of the steam. check that your pressure is as low as possible as well.--nbc
@ March 7, 2011 4:43 PM in Need Buffalo, NY contractormaybe tim should advertise his services on this web site! you are not the first from buffalo to be looking for professional help!--nbc
@ March 7, 2011 12:36 PM in Capped Riserit sounds as though the cap is leaking, possibly due to over-pressure. have your steam man check the pressure and reduce to under 2 psi MAX. reducing the pressure will reduce fuel cost as well [even more savings by further pressure reduction with a vaporstat].
naturally, the cap should be reset with some new teflon tape.--nbc
@ March 7, 2011 12:17 PM in Need Buffalo, NY contractorif you can describe the symptoms here maybe we can get you through for a few days or more with a simple but temporary fix.
when you say "short-cycle", is that caused by low/high water, high pressure, or...?--nbc
i am surprised that your current steam man hasn't suggested someone else as a stand-in.
@ March 7, 2011 7:26 AM in New Boilers for Steam System Previously Converted to Hot Waterif those boilers are 1.50 mbtu each, then perhaps they were over-sized. most likely, they were sized according to the old steam boiler.
i doubt if the landlord will have the temerity and smarts to at least consider the possibility of steam, unless he were to consider the cost of repiping the under-sized returns! in fact i wonder if anyone will think of doing a heat survey.
the clause in the lease which "excuses" poor heating performance could be against the landlord tennant laws in many states.--nbc
@ March 6, 2011 11:35 PM in ornate radiatorsvery nice, and i expect that most of that price is for the delivery! do you have 1-pipe [as they are], or 2-pipe--nbc
@ March 5, 2011 8:10 PM in Burnham V11 Steamerit must be difficult to be the "relief hitter" in this game. if something goes wrong who would get the blame?
can you get a letter from burnham showing that your service will not void the warranty [as if it were the result of some sort of exam you have passed]? how old is this boiler?
as it is another mechanical part to malfunction, the zone valve could be replaced by trvs, or at least exercised more regularly to keep them working. the church might be saving very little by zoning, and should have all service done by one person.--nbc
@ March 5, 2011 7:30 PM in Two equalizers?you should be able to get the installation manual from the mfg's web-sight. study the required piping diagram and compare it to what you have. those mfg's requirements are the minimum required, and will show you the relationship with the second riser.
a drop-header would be a big help on this one, to fit every thing into your constricted space, as jimmy says. there are plenty of pictures of them here. i don't think there is any necessity for a second equalizer as long as the one there is big enough.--nbc
is this the right one?: