Joined on August 11, 2008
Last Post on September 16, 2014
@ February 22, 2014 8:24 PM in Thermostat calling for heat; boiler does not come onCloser....that's .1 and .5
@ February 21, 2014 1:39 PM in taco zone relay constant hum soundJoe is from Taco, the manufacturer of the relay. If he says you will not have a problem with the replacement, trust him, and give him a call.
@ February 21, 2014 12:10 PM in taco zone relay constant hum soundWe see complaints here, all the time. One of the only manufacturers that will always respond to a complaint, and go "above and beyond" to make it right, and do the right thing, is Taco. Joe, you and your company are to be commended. Here's to a U.S. manufacturer that cares!
@ February 21, 2014 11:45 AM in taking a hot water zone off of a steam boilerAt some point air got pumped into the zone. Since it is not pressurized, there is no way to get the air out. Use garden hoses to power purge it. This will deal with the issue at hand, not the ongoing problems it will have.
@ February 21, 2014 11:21 AM in Not Enough Radiation?The thickness of the wall in the photo, suggests they may have built walls within walls. I read a posting here( to which someone from Burnham was responding) that stated that just stacking convectors produced little difference in output, because it just created interference to convective air flow. The addition of the fans would counteract that though. I don't know how you would calculate the output of the modified emitter, other than trial and error. Without a proper heat loss,there is no way of knowing whether you could get close to correct by just increasing the output of the existing enclosures.
@ February 21, 2014 10:10 AM in Not Enough Radiation?The output of those elements will be similar to those of standard baseboards. You need to do a heat loss for the room. Try as you may, "you can't make a silk purse out of a sows ear".
@ February 19, 2014 9:49 PM in Pictures of existing system that needs replacementWet base boilers weigh close to double, but that thermal mass is a good thing. If I remember correctly, my 5 section series 8 was 750lbs skidded. I lowered it off my pickup with a die table I borrowed from work. Got it hanging over the basement stairs in the Bilco door. Then tied braided nylon rope to the skid and the back of my truck. I tied the rope taught, then got in the truck. I put it in neutral and put my foot on the brake. I told my buddy to push it, so it teetered down the stairs, and get out of the way. I heard this ZING and then I could feel the weight pulling the truck. I eased up on the brake and the truck moved back about 6 inches.
I failed to consider a couple things...the change in direction meant the rope got loose, and the nylon rope stretches a lot. I knew it wouldn't break. My buddy said it was unbelievable. It took off down the stairs like a shot, then slowed down and stopped about 6 inches above the basement floor. We stopped and had a couple beers after that one.
@ February 18, 2014 6:54 PM in Steam boiler replacement quoteWas that 6 inches? My monitor gets too blurry to distinguish one or two hash marks. Or, maybe it's my eyes.
@ February 18, 2014 11:30 AM in Steam boiler replacement quoteBob......Different wording...same message.
@ February 18, 2014 11:28 AM in Steam boiler replacement quoteI think the amazing part, is that he was unable to find anything wrong with the existing system.....Nothing! Just connect it to the existing piping, cut him a check, then try to find him. I think the most important thing, should be the statement...The boiler will be installed to manufacturers specification.There are postings here daily, from folks that have boilers hooked up exactly as you were quoted. The boiler are not even skimmed ,hooked up to existing piping with no header, or no equalizer. The mains have sags in them, and no main vents.
If the contractor will not sit down and discuss the whole system with you.....Show him the door.
@ February 16, 2014 8:00 PM in clanking soundsThe neighbor had his valve replaced. I'll bet they jacked the radiator, and lost its pitch.
@ February 15, 2014 7:45 AM in New furnace started kicking after a season of quietPut a carbon monoxide detector in that basement.
@ February 13, 2014 5:44 PM in 2# gas line for 600, 000 BTU'sYou have plenty of available gas.Order what you need (within the limitations of the meter), and the gas fitter will sort it out. If you have a regulated manifold, he may have to upsize the regulator, but it's all do-able.
@ February 13, 2014 3:34 PM in 2# gas line for 600, 000 BTU'slike you have 1/2 lb. in the house. For instance, I have 5 lbs up to my meter, and 1/2lb coming into the house. I have to size to 1/2 lb.
@ February 13, 2014 2:18 PM in Meet The CozyHave you ever taken apart a really old mechanism, and been amazed at how "beautifully simple" the design was? That's what you're striving for. I know it's not always possible, but you want people to look at your work, and say,"why didn't I think of that"?
@ February 13, 2014 10:52 AM in Meet The CozyIt makes more sense. I can't tell from the pictures where they reside though. And what about when they room is not calling for heat(no fan)?
@ February 13, 2014 10:39 AM in Meet The CozyThink they live in, and pull heated air. You're pulling cooler air to cool the PC components. Different application. I think.
@ February 13, 2014 10:31 AM in 2# gas line for 600, 000 BTU'sThis should give you the basics of how to size it. You should be able to get a 2lb. chart online. http://www.youtube.com/watch?v=mPjEllrv0Bs
P.S. Provided the instructor doesn't put you to sleep. Mr. Monotone himself!
@ February 13, 2014 9:46 AM in Meet The CozyHave you had issues with heat and electronics? How are you not burning up fan motors? Are components field servicable, and reasonably priced? Does it pass the "Mom" test? Could my mother, easily replace any component?
@ February 12, 2014 9:52 PM in Meet The CozySeems like a good product, that I was completely turned off to, by the soliciting of donations.Donate your money to a homeless shelter, so they might be able to put oil in the tank. Sorry, trying to keep it real.
@ February 12, 2014 2:09 PM in Is this main circulator grossly undersized?Is 40000 btus for 3/4" pipe. So, your zone would appear to be grossly over-sized. You might want to rethink zone distribution before circ sizing. When you start daisy-chaining many emitters, you have to allow for the DT, and add emitters accordingly downstream. I'm sure the pros will elaborate on this, I am just a homeowner.
@ February 2, 2014 7:26 AM in Hot water baseboard heatingOver 500 posts and nothing is getting solved because the ABC's keep getting jumbled. Start a new post, because that is where this one is anyway.