Joined on February 17, 2009
Last Post on March 1, 2014
@ December 17, 2013 10:56 PM in Importance of combustion gas testing?I have always used my eyes first, and then the tester. I won't bother testing a flame that looks to be impinging, lacks air, or is too "clean". Nothing wrong with knowing what the right fire "looks" like. I think techs should know what to look for, and not just flip the switch and jab a Testo or something in a smoke pipe hole. If he tested and shared the results, I would see no wrong done here. All manufactures setting are starting points. I like to see that starting point, the adjust and test from there personally.
@ December 17, 2013 10:44 PM in Oil line flare fittingsBeckett part# 5669, that is what you need. It will be a Honeywell delayed oil valve, 2 nozzle lines, 2 1/8" brass 1/2 flare elbows, and the body mounting kit. How about going with Clean-cut pumps? Also you asked about the supply line from the tank to burner. What will the firing rates be per burner? You said there would be a total of 3. You may need 1/2" line
@ December 17, 2013 10:38 PM in Beckett AF Problemfigured it was the cad cell relay, but missed that it was a steamer, so asking about "T-T" must have been out of left field. Good luck
@ December 17, 2013 10:34 PM in One Pipe system - water hammer/lots of water from ventsam I seeing Taco oo7, and extrol tank? Is one a steam, and the other forced H/W?
@ December 15, 2013 4:47 PM in Beckett AF ProblemHow is the "T-T" wired, or is it jumped? I would say bad 8184G. Go with a Genisys control. Jumping "F-F" and starting the burner will not trouble shoot it
@ December 15, 2013 11:27 AM in weil-mclain WGO-4 boiler... can it do DHW?does it have a tankless coil? If it is a WTGO-4 yes, if not, then it is a cast over. You can go indirect off that boiler. It would be like adding another zone.
@ December 15, 2013 10:47 AM in Hot water heatit is monoflow, I would return it and get 3/4"
@ December 15, 2013 10:22 AM in Chimney Liner Needed for Oil Burner?Is the chimney unlined? Has the unit been upgraded to one with a much lower stack temp? Signs of condensing? Any hidden plugs/caps up in the house where there was a stove? You should hire a chimney inspector, and not just a sweep to determine if it is your best interest
@ December 15, 2013 10:15 AM in Beckett Burner irregular tripsThat could mean 2 things. Either there is no ignition on start up, or it just locks out occasionally. Never easy giving advice just from a post. I am a Beckett fan, but like Carlin EZ-1 on certain units. They have come a long way from the old US Carlin, and 100 CRD's. I also like Riello, but they only run well on certain units. Also, non PSC motors with starting switches are not always easily trouble shot with an OHMs meter, and the new controls will not always help to trouble shoot by viewing the history. Sometimes you gotta just roll up your sleeves.
@ December 15, 2013 10:03 AM in System 2000 controlerI would say no. One power head per terminal
@ December 15, 2013 9:58 AM in Cad Cell Problem?but I would say it is either a bad zone vave, or primary control. The cad cell eye will only lock it out, and not short cycle/on & off. I would call a tech. Pics will help also. Good luck
@ December 14, 2013 4:29 PM in 10 seconds of oil smell when oil furnace starts upcrack in the heat exchanger? I would have it checked. Could be an inspection door, or clean-out access port, delayed ignition, rotted or disconnected smoke pipe, partially or plugged chimney, down draft, and countless other causes. Have it checked by a pro.
@ December 14, 2013 1:53 PM in Beckett Burner irregular tripsI also find that. It can be caused by a a few different issues. One is the gun adjustment, or "Z" dimension. The shorter the tube, the harder the gun is to get in and out. Many guys will loosen the screw, and pull it back so it will go in and out easier. Not good. Another is impinging, and another is from the flame floating away, and not burning on the endcone itself. This can be from low pump pressure, improper air adjustment, wrong endcone , defuser, etc. Beckett AF/AFG is an excellent burner, and like most others, will only operate as good as the last tech to service it
@ December 13, 2013 6:02 PM in Beckett Burner irregular tripsreplacing the control to one that will interrupt the ignition, or shut it off after light off, if you go electronic ignitor. These do not like constant duty
@ December 13, 2013 5:59 PM in Boiler Pressure Spike while under heatadd an isolation valve. Although nice when replacing an extrol, by just closing it with pressure on the system, it is only trapped in the tank, and you won't get an accurate PSI reading. Shut the valve off, and remove the tank. You will see what I mean
@ December 13, 2013 1:31 PM in Boiler Pressure Spike while under heatIt may be unlikely, but does the boiler have a tankless coil in it, or have an indirect? May be a pin hole, or even a bad feed valve
@ December 13, 2013 1:29 PM in Beckett Burner irregular tripsWhat is your pump pressure, and what is it mounted to for a unit? Wrong nozzles, weak spark, draft issues,and improper air and "Z" dimension settings will all cause this to happen. What control is on this burner? One with a pre-purge, and interrupted ignition would be a big plus, as well as a post -purge.
@ December 13, 2013 1:09 PM in Boiler Pressure Spike while under heatI've had some that the diafram would not compress. Had air, but wouldn't release from the inner sides of the tank. I would first take the pressure off the boiler, to zero, then test the air pressure. Should be 12-15 with zero on the boiler side. Also, any change to piping? Is the tank isolated between a flow check and zone valves? Pics will help
@ December 3, 2013 9:13 PM in Fan/limit rising with fire offI wouldn't rotate the fan limit manually. First there are instructions on it that tell you not to, second, it will throw your the control off even more. Replace it if it is in question
@ December 3, 2013 8:59 PM in Beckett 7505 120V GeniSys Controlare you trying to monitor,or reprogram the control? This is a great control by the way
@ December 3, 2013 8:56 PM in Oil / Gas Nozzle conversion - HELP!I would start from scratch here.
@ December 3, 2013 8:51 PM in Carbon Monoxide Issues - HELP!here on Cape, it would have failed. I would see to it if it was in my customer base