Joined on November 10, 2004
Last Post on November 18, 2005
@ November 18, 2005 2:53 PM in GB in the AdirondacksAlways good to see pics from the field. You guys are lucky to have Rick out there. I will look forward to the N&S visit.
@ November 3, 2005 7:41 AM in More GB MagicIt is so nice to see great equipment professionally installed. You guys in NY have something to be proud about. I am looking forward to more posts and pics from other areas. We will be continuing to bring more innovative products to market over the next few years. Our website will announce new product as it becomes available so keep checking us out. Thanks, Dave
@ August 25, 2005 10:49 AM in new venting code in MASSJuly 27th Division of Professional Licensure has made this official
@ August 8, 2005 8:40 AM in Does New Energy Bill apply to boilers?What section did you see that in Ted?
@ July 22, 2005 8:08 AM in GB142Who makes the nuetralizer? Is the nuetralizer a requirement where you are?
@ July 19, 2005 12:44 PM in Buderus Logamatici would have powered 3 and 5 respectively for each unit off of terminal 63.
@ July 19, 2005 10:45 AM in Buderus Logamaticline in to 1 and 2, wire 63 to terminal 3. circ on terminal 4. make sure the circulator load is not more than 5 amp.
@ July 18, 2005 12:52 PM in buderus or viesmanWe offer training every month. I dont think the contracting public wants us to decide who installs and who doesnt. We leave that question to the trades. All we can do is try to educate as many as possible. check our training site on the web page for information.
@ July 18, 2005 10:55 AM in Working Mans BluesThats why i moved from NY to NH. Tired of paying into the NY tax which is generally wasted.
@ July 13, 2005 7:48 AM in outdoor reset for buderus gb142Our version of outdoor reset is not available yet. The Tekmar 265 and 263 are in the near future. The EM-10 is not here yet. As i said in the past, i will provide details asap. Thank you for your interest. Our website will also reflect any changes as they become available.
@ July 11, 2005 2:59 PM in GB142 and Mass. ApprovalIt can be installed to do your heating and domestic hot water. We are pursuing NYC approval.
@ July 7, 2005 2:02 PM in Kettling noises from cast iron water boilersThis could be a flow issue or impingement coupled with flow issues. When is it happening? Is it at initial start up or is it occuring at shutdown?
@ July 7, 2005 11:58 AM in GB142 and Mass. ApprovalIt is approved as a heater. In the near future it will have the H-Stamp and be approved as a boiler. We will only offer it as a boiler when that approval is finished. This should avoid the confusion as to which one to order as there will only be one version.
@ July 6, 2005 2:33 PM in GB142 and Mass. Approvalapplication is in process and I will advise asap.
@ July 6, 2005 10:32 AM in GB142 and Mass. ApprovalWe have Mass. approval on the GB142 condensing heaters as of today. I promised to update all of our friends here on the wall. Its a good day in Mass.
@ June 21, 2005 8:30 AM in Small boilers again.............you can control the output of the GB142.
@ June 20, 2005 10:25 AM in Boderus, WM, Dual Boilers...Helpyour choices with us are the GA series or the GB series. Either one will do the job and can be direct vented. Make sure of your load before buying. As far as parts and service; you can check our website for distributors in your area. WWW.buderus.net.
@ June 20, 2005 10:19 AM in Buderus Here I ComeWe will let you know when you get here.
@ June 17, 2005 8:18 AM in Buderus GBAsk Buderus what the combined pressure drop is for your application. The GB has significant pressure drop. Probably why we make circulator selections that seem oversized.
@ June 16, 2005 2:51 PM in Buderus GBWhat is the pressure drop on the GB? You might want to consider that before making a circ selection.
@ June 16, 2005 8:21 AM in Buderus GBWorks fine with our tank of similar size. But we do have a larger coil diameter i believe.