Joined on June 23, 2005
Last Post on January 25, 2014
@ March 16, 2010 8:07 PM in When is wrong, not really wrong?see it all the time . The customer always believes the cheapest price . Pay cheap get cheap . Once was told by a home owner that he PAID extra for the good Copper header.
@ March 14, 2010 12:13 PM in Steam Boiler pipingLow-pressure steam February 2010 Page 36 . What do you think
@ February 16, 2010 7:26 PM in Plugged circulatoron a radiant system . this is the 3rd pump that has been found in this condition .Other problem was rusted extrol tanks .The tubing is" onyx "with a oxygen barrier .But the supplier has told me that the tubing is "the good stuff" Any other suggestion ,besides the tubing.
@ February 12, 2010 6:57 PM in Green SteamDan , just finished the book . Great job as always .Loads of great information.
@ February 6, 2010 7:05 PM in NO vents onNo , it has beenbutcher years ago . Everything was removed ,
@ February 4, 2010 7:32 PM in NO vents onthe entire 2 pipe system . There are no cross overs . The system works great , were does the air go?
@ December 31, 2009 6:56 PM in Happy New Year !and yous , A Happy New Year I hope the new years is better to all of you then the oldf was
@ December 29, 2009 6:55 PM in Indirect radiatorsfound in basements,usually covered in wood and ducted to the outside . Of course no longer ducted outside . The EDR is usually noted by the size of the feed . Anyone know the edr of 1 1/2 & 1 1/4 pipe
@ December 21, 2009 5:22 PM in Am SteamIts a non-electric zone valve ,the head is bad ,anyone know of a replacement head or who makes it. And to beat all its for hot water
@ December 7, 2009 6:02 AM in Clock thermostats on radiant zones?Try ,telling him about the advantages of set back
@ December 1, 2009 5:10 PM in Problems with New Steam BoilerGo to the instruction , Its all there . If it matchs your ok , if not get them back to make it right
@ November 23, 2009 11:53 PM in new radiator - clangs! bad pipe?one pipe or two. I would NEVER have split the pipe
@ November 20, 2009 2:33 PM in Clean new pipe and fittings first?I use Arm & Hammer solution to clean pipe B4 installing
@ October 15, 2009 11:55 PM in Gas furnace (3 zones) -shuts off after 2 minutesthe water pressure . Should be about 12psi , if you done have pressure the water can't move .