Joined on August 13, 2009
Last Post on March 2, 2014
@ July 4, 2013 9:20 PM in What type of dehumidification systemshttp://www.tech-4-you.com/ESC/PDF/Entergy/7_Entergy_Novelaire.pdf
@ July 4, 2013 12:31 PM in What type of dehumidification systemsI dont know. I would imagine the type system that is circulated through the floor and walls, similar to radiant heat.
@ July 4, 2013 9:32 AM in What type of dehumidification systemsare they using with radiant cooling?
@ June 27, 2013 3:00 PM in 6" Boiler Exhaust w/ 5" chimney liner. how bad is this?Thank you for the info Charlie
@ June 26, 2013 7:19 PM in 6" Boiler Exhaust w/ 5" chimney liner. how bad is this?Is there a difference in btu capacity between gas and oil?
@ June 24, 2013 10:08 PM in 6" Boiler Exhaust w/ 5" chimney liner. how bad is this?According to that chart if I were to install a Buderus 115 ws, I would need to increase the 5 inch factory collar to 6 inch.
Obviously Buderus feels comfortable firing 1.10 gph into a 5 inch outlet.
@ June 23, 2013 10:13 PM in 6" Boiler Exhaust w/ 5" chimney liner. how bad is this?that differentiates between the two. Could you please post your chart?
@ June 23, 2013 7:36 PM in 6" Boiler Exhaust w/ 5" chimney liner. how bad is this?according to this chart.
@ June 23, 2013 7:10 PM in 6" Boiler Exhaust w/ 5" chimney liner. how bad is this?Liner capacity is based on vertical length, diameter and horizontal distance . Also based on natural or induced draft. It is best to install the proper size liner and not just use what the manufacturer welded to the top of the boiler.
You will notice manufacturers will use the same size flue outlet on several of the same series boilers before jumping to the next size.
So I am not saying yours is correct but it very well could be.
Give us the length of the chimney and the length of the horizontal flue and the input of the boiler and we will tell you if the 5 inch is large enough.
@ June 19, 2013 8:22 PM in Bridging the gap Hydronics to ACyour hydronic customers since they dont have any duct in the house.
It keeps me busy all summer long.
I use to handle Fujitsu but what I have found is that after several years the Fujitsu plastic really yellows.
So as of the last few years I have been installing Comfort star and Samsung.
The Comfort stars work really well and internally are identical to Samsung but they only come in white.
The Samsung Vivace is mirror black just like the TV.
I find you don't need gauges since the txv is inside the condenser unit. That is why you insulate both lines. What you do need is a good automatic scale and a small reclaimer.
I also just purchased a UNIWELD 2 stage vac pump that weighs 9 pounds. I also keep a 300 ft tank of nitrogen in the shop and refill my 10 ft tank after each job. No sense in dragging around a 35 lb vac pump and a large tank of nitrogen for a mini split.
You will be drilling a lot of 3 inch holes through a lot of different materials, so be prepared with an assortment of bits.
I have also found in homes with pets and some without that the squirrel cage blower will have to be cleaned after a couple of years. After watching guys struggle with a bottle brush or making a mess on the wall I have found it is best to remove the blower wheel and use a garden hose to clean it. It is not that complicated but I would recommend taking your first one apart on a bench in your shop until you become familiar with it. Long magnetic screwdrivers really help as does a small magnetic dish.
Also after taking them apart you will find they all roll off the same Chinese assembly line using the same parts.
You will also need a few adapters( 5/16 OR 1/2x20 UNF) core remover and a 5/16 low loss x 1/4 flare adp. Also because there is no low and high side you will need a dye injector and you will need another 5/16 low loss x 1/4 adapter for that.
I love installing ductless and my customers love it even more.
@ June 13, 2013 6:42 PM in How the Europeans do it?Here is a short clip on how most "Europeans" feel about Germany
@ June 13, 2013 6:30 PM in How the Europeans do it?very popular in countries like North Kore and China. What they do to deserters is arrest their family.
@ June 13, 2013 9:07 AM in How the Europeans do it?How were you going to enforce that rule? Beatings, jail time....LOL
@ June 12, 2013 9:34 PM in How the Europeans do it?I don't know about that Mark. I don't feel college degrees are as important in our field as is natural intelligence.
In many fields especially ones where facts and figures need to be repeated to the point of nausea , a college degree can be beneficial. Probably a photographic memory even better. But in our situation where everyday brings new places with new situations the ability for critical thinking is more desirable.
Personally I find the best apprentices(not always) have a n IQ of 120 or better( no higher than 140 or they detach) a mechanical aptitude of 95% or better with high scores in spacial relations.
This criteria is much more desirable in our field than a run of the mill college degree.
So why shouldn't someone with high natural intelligence make more money than a simple college degree? Many MENSA members are high school dropouts.
@ May 31, 2013 4:19 PM in How critical is this new 410a flareI guess Ill let go of the hundred bucks.
@ May 29, 2013 8:51 PM in How critical is this new 410a flarehttp://www.ebay.com/itm/YELLOW-JACKET-60280-FLARING-TOOL-HVAC-/130917225304?pt=LH_DefaultDomain_0&hash=item1e7b465358
I agree it is an excellent tool, I just want to know what is the difference between this and the new one. Cant seem to get a clear answer on this.
@ May 29, 2013 5:02 PM in How critical is this new 410a flareI have an older yellow jacket deluxe flare tool that I have been using for many years.
I can honestly say I have never had a leak in one of my flares. But I keep hearing that you must use the new deluxe flaring tool on the new mini splits.
I have even taken my older unit to the supplier and made a flare with mine and then with their newer unit. I am really hard pressed to see a difference in the two.
What is the difference between the Two and how critical is this? Who here has already purchased the new tool and can really attest to it working better?
@ May 28, 2013 8:15 PM in propane tank locationread it, there are exceptions in the text
@ May 19, 2013 8:30 AM in Longest lasting indirectsIf you break something, then you stimulate the economy by hiring people to fix it.
Start thinking Water Conditioning systems and Graphene base RO systems.
@ May 13, 2013 7:00 PM in duct sizingIt works well and is quick and easy. Its in PDF so print all you want.
@ May 13, 2013 6:39 PM in Hot water recirculation do they save money?about being tankless LOL
@ May 13, 2013 4:58 PM in Hot water recirculation do they save money?the energy your consuming with a circulator.
Turn on your water heater until it goes off and dont use any hot water at this point.
Place a temperature probe against the side of the tank(inside of the insulation) and read temperature. Turn on your circulator and time out for 1 hour and record your temperature drop. Take your size of your tank in gallons x 8.3 will give you pounds of water x temp drop will give you BTUs lost per hour.
Now do it without the circulator to get a base mark to compare.
Once you have this info it is easy to compare it to the fuel your using.
Dont forget to also add the wattage of the pump to the cost.