Alan (California Radiant) Forbes
Joined on August 14, 2009
Last Post on July 6, 2014
@ April 6, 2010 11:12 AM in New "Lead Free" LawOh, joy..............California has a new "Lead Free" law that reduces the amount of lead allowable on wettable surfaces from one-half of one percent to one-quarter of one percent. And this law is COMING YOUR WAY. It's already law in Vermont.
It's a good law since lead does nasty things to our bodies when we ingest it, but for those of us heating and plumbing contractors in states at the forefront of the movement, very little is available on the suppliers shelves that conforms to the new standard. Our suppliers have us signing releases when we buy cast fittings, valves and pumps, saying we will not use them on potable systems.
I wanted to buy a Taco X-Pump Block for a job. I can buy an "old" one, but my supplier doesn't even know when "new" ones will be available.
And all that old stock on your shelves waiting for a job? Better start using it before the law comes to your state.
@ April 5, 2010 12:41 PM in WM Steam boiler installNice work!
How would you wire the hot water aquastat?
@ April 4, 2010 7:59 PM in Manifold & Actuator Questionare normally electrically operated (24 volts) by a thermostat. So, to answer your question: yes, they are (indirectly) thermostatically controlled.
@ March 31, 2010 5:12 PM in Munchkin F00 Error MessageI didn't try to jump T-T, but I did jump the high limit and still got the error message.
The boiler is a few years old, so I don't think the problem is with polarity, but bleeding voltage may be happening. If the Munchkin is able to "see" a different voltage coming back when the end switch closes, it may be the cause.
@ March 31, 2010 11:53 AM in Munchkin F00 Error MessageThere is an indirected connected to the system and as soon as the T-T leads were disconnected, it started making DHW.
@ March 30, 2010 6:20 PM in Munchkin F00 Error MessageI've been serving Munchkins for awhile now, but this was a new one.
"No Heat" call from a new customer. F00 error message which translates to "high limit exceeded". This error message persists after the 925 controller is reset and when the boiler is cold.
HTP tech. support tells me to remove the T-T connection to the boiler at which time the boiler comes on. He says the problem is not with the Munchkin, but with either the zone valve controller (Taco ZVC 404) or zone valves (Taco ESP or EBV style) which makes total sense. Turns out the owner has been having problems with the zone valves.
So, what is it in a zone valve or controller that would make a Munchkin 925 controller come up with an error message? The Munckin sends out one leg of 24 volts to a pair of isolated contacts that close on a call for heat. What goes wrong?
@ March 25, 2010 9:19 PM in Secret life of low temp panel radiators ?but they have limited sizes. For more of a selection, check out Runtal:
Even though they are called commercial/institutional, we still use them in homes.
@ March 25, 2010 3:45 PM in Help IDing Radiatorhttp://www.oldcastironradiators.com/CastIronBaseboards.htm
@ March 19, 2010 3:05 PM in Sizing Pump for Hot Water Radiators.If they are old-style column-type radiators, the pressure drop is minimal since the passageways are large.
Figure your pressure drop through your boiler and piping and then add a couple of feet of head.
@ March 19, 2010 1:16 AM in Efficiency: Combi Core Vs. Boiler and DHW storage tank?The boiler is more expensive until you figure the replacement cost of the CombiCor boiler. All the ones I (and many others) installed fail at the heat exchanger within the first few years. I'll be in San Francisco next week to replace one with a regular water heater and an external heat exchanger (Taco X-Pump Block).
I've had very good luck with the Triangle Tube Excellence combi boiler:
And talk to Paul Pollets; he's in the Seattle area and know his stuff.
@ March 15, 2010 1:26 PM in OT rain ,flooding how badLots of rain here in the Bay Area; something we haven't seen in quite a few years.
This would have been normal 35 years ago.
@ March 12, 2010 12:25 PM in New to steam - need help with start upLooks like someone came in and removed the water supply line, maybe for scrap copper?
For a start:
- Provide a water feed with a valve to the boiler
- Fill the boiler to the "water line" and make sure it shows up on the sight glass.
- Pipe the low-water cutoff (LWCO) drain valve to a drain, open the valve and let the water run until it's clear.
- Get a copy of the installation manual; I'd say it wasn't installed per mfg's. instructions.
@ March 11, 2010 7:47 PM in BookmarkingYou did that for me? I just changed my will. You get half of everything I own when I croak.
@ March 11, 2010 10:52 AM in BookmarkingHey Dan:
It's just a small issue, but I've noticed a few times that the URL for different forums will change; most recently, the old URL ending: "THE-MAIN-WALL" changed to "THE-WALL".; Strictly-Sream" changed to "Steam-Heat", etc. so when I go to my old bookmark, I get an "Oops - You have attempted to go to a page that does not exist." message. You messin' with us?
@ March 11, 2010 1:27 AM in cutting copper tubing with shearsBut the movie clip on Youtube pits the tool against a minicutter. Minicutters are slow; why not put it up (legitimately) against a regular tubing cutter? Kind of lame.
@ March 9, 2010 9:48 PM in Re-piping JobNice work, Bob. Looks like you made many improvements to her system and she will be enjoying a quality heating system for years to come.
My only comments - if you don't mind me saying so and these are just my personal preference - are that I would have used cast fittings instead of malleable and I would have used a bullhead tee at the take-off and brought the 3" main down to it. It would have slowed down the steam a bit more.
I like the fact that you took extra time to install a drop header.
@ March 8, 2010 12:12 PM in Thermostat or not?the boiler is perfectly sized to the heat loss of the building, you need a thermostat. Without the thermostat, the boiler has no way of knowing how warm it is inside the building. Without the thermostat, the rooms will overheat.
The heat loss of the building is dynamic; low heat loss when outdoor temperatures are mild and a high heat loss when it's freezing outside and the thermostat (in your case) is the only way the boiler knows what it's like out there.
@ March 8, 2010 11:23 AM in Bradfordwhite combicoreAll the ones I have installed have failed; typically at the heat exchanger. Others have had the same experience. It may be the water, it may be the heat exchanger material, but I don't use them anymore.
@ March 8, 2010 11:15 AM in flooded radiatorsOne-pipe steam is meant to work at very low pressures; that is why the pipes are so large. Many of your Mother's problem will go away once the pressure is set properly.
Pressuretrol should operate between .5 and 1.5.
Vaporstat should operate between 4 oz.and 10 oz.
@ March 5, 2010 4:16 PM in Water Heater for Slab HeatIf you have a water heater dedicated to the radiant slab, i.e. no DHW, then you don't need a HX.
@ March 5, 2010 3:42 PM in I need a computer program for PEX tubing layoutsis an excellent product. When you load the program, it will ask you if you want to check for new versions. The upgrades are free and I look forward to downloading the new one on Monday.