Joined on September 3, 2009
Last Post on March 9, 2014
@ February 14, 2014 11:04 PM in 007 CAPguess a 100 watt light bulb and a keyless bulb holder. Riello allows this to be used as a capacitor on their burners in a pinch.
@ February 13, 2014 8:21 PM in New furnace started kicking after a season of quietpiping is not right. No equalizer....hence the water level in the glass is all over the place. And maybe the reason the water hammer.
@ February 13, 2014 7:42 PM in New furnace started kicking after a season of quietpiping is wrong then raising the water level will throw wet steam into the main and cause water hammer. Do you have any pictures?
@ February 13, 2014 6:56 PM in New furnace started kicking after a season of quietBoiler is hammering. Adding treatments to the boiler water as a general rule will not help. Skimming is the best treatment. Get any oils out of it that are in there.
@ February 13, 2014 6:51 PM in 2# gas line for 600, 000 BTU'sFine. Run the 2# line from the meter. the regulator will have a red dot on it for a 2# set up.
Once you get into the boiler room hook it into a Maxitrol 325-7A
Then pipe out to each appliance as if the meter were right there.
@ February 12, 2014 9:52 PM in Radiators Hissing and steaming after insulation appliedYou just need to go the next step. The boiler is running on low pressure , its safe. If you want to quiet the radiator then twist the air vent shut or flip it upside down. Did you check the find a contractor listing?
@ February 12, 2014 9:03 PM in Radiators Hissing and steaming after insulation appliedyou need to either add some main vents in the basement or replace them.
They are larger than the radiator vents. Usually they are found at the end of the mains. Where are you located?
@ February 12, 2014 6:43 PM in Cold dayDo the primary loop w/ a 15-58 Then install another one on the primary loop. The primary should be full size. the piping off the main loop should be 1 pipe size less that 1/2 of the main. so if the main loop is 2" your piping off the primary loop should be 3/4"
@ February 11, 2014 9:43 PM in biasi b-3If you did the heatloss and your hot water needs are not crazy.
@ February 11, 2014 7:25 AM in I don't like my new boiler! oh noboiler w/ a Riello burner. Its not that bad. Riellos do have a unique sound...What is the model of Buderus boiler? 115? 215?. Now before having the entire boiler removed you may want to see if a Carlin burner can be put on instead. (it would depend on the boiler model) It may help.
@ February 9, 2014 6:24 PM in Biasi boiler review?when people bomb throw here and then never respond to other willing to help fix a problem...
@ February 8, 2014 11:44 PM in Boiler Bypasshttp://www.amtrol.com/support/extrol_res_sizing.html
@ February 8, 2014 10:56 PM in Boiler Bypassis really the way to go. This way you provide some measure of protection to the boiler and can control the flow to the radiation. It is very important to try to mimic the gravity flow out to the system Over pumping will result in poor heat transfer and a less efficient system. That looks like a #30 extrol tank...generally not big enough for a gravity system...
@ February 8, 2014 2:04 PM in Master Plumber/Heating Contractorat 180F water temps it is approx. 600 btu/ foot
@ February 8, 2014 11:24 AM in Combi Boiler Recommendationexpansion tank that is water logged. Give us some more info plz.
It may help to start a new thread....
@ February 7, 2014 5:41 PM in Crown boiler doesnt keep up with thermostatwater pressure that's gallons of water. And that's A LOT of water!
Its not piped right. Not vented right. Who cut the draft hood! No Hartford loop. The Header is improperly sized....
Its not insulated...UGH. What a mess. You need a steam expert to start again.
@ February 7, 2014 5:32 PM in Crown boiler doesnt keep up with thermostatlots of pictures... they say a lot.
@ February 7, 2014 5:27 PM in Biasi boiler review?two different units here.... The original posters were talking about the B series oil fired boilers. DIY is talking about a gas fired wall unit. What type of issues? Is this a new boiler in a New system or a boiler replacement in an existing system? What type of issues? Do you have pix? Proper installation is a must w/ the new wall hung boilers. Any electrical board could get fried by a electrical surge....
@ February 5, 2014 9:28 AM in What brand of indirect hot water heater would one recommend ?using the Weil Mclain Aqua plus series for over a year noW. 2" foam All stainless and it has an Anode rod! It has a coil design for the HX vs the tank in tank set up.
@ February 3, 2014 5:05 PM in Not getting enough heat.flows upwards its backwards. Should be down going back into the boiler.
@ February 3, 2014 5:00 PM in Can 1 radiator system be converted to 3 separate ones?it just depends on how much you want to spend to do it. You are looking at a near repipe and having to really get 3 new boilers w/ separate meters.