Joined on September 3, 2009
Last Post on April 18, 2014
@ February 19, 2014 8:26 AM in No luck with my Noritz questioncheck you incoming gas pressure and you manifold gas pressure? How about your incoming water temps?...the water is much colder this time of year.
@ February 17, 2014 11:06 PM in Poly Pro venting....your not supposed to need it by the leaks cause me to lose confidence it the stuff.
Yes its it pitched back towards the boiler.....as per instructions.
@ February 16, 2014 8:53 AM in clanking soundslikely you radiator needs a bit more pitch towards the valve. That sound is water hammer. there is prob a puddle of water in the bottom of the radiator. I would have your neighbor keep that valve open... the vent is how you control the amount of heat from the radiator...not the valve.
@ February 16, 2014 8:47 AM in Which of these two setbacks is more economical?if you have the vito 200 why mess w/ the boiler reset.
@ February 15, 2014 8:55 PM in Viega press sleevesa lot like them...
@ February 15, 2014 4:25 PM in Running Out of Hot Water With a Megastor -40an aquastat issue. may need a cup of coffee!
@ February 15, 2014 4:24 PM in Solar Thermal is Deadhttp://www.foxnews.com/us/2014/02/15/world-largest-solar-plant-burning-up-birds-in-nevada-desert/?intcmp=latestnews
140,000 home w/ electric power.
@ February 15, 2014 3:04 PM in Poly Pro venting....Anyone been having issues w/ polypropylene venting connections? I have a couple boilers out there that use the concentric set up. and they drip condensate back into the boiler. When the boiler is all sealed up its tough to see there is an issue....until you have a bit of a mess.
I installed the venting w a bevel on the male end and used a bit of spray silicone to make sure it went together well. I am about to give up and use high temp silicone caulking. The leaks tend to happen on the horizontal runs.
@ February 15, 2014 7:42 AM in New furnace started kicking after a season of quietinstall manual. see page 19
They are pretty specific on piping just so, because the newer boilers have interior spacing that is much narrower than the old boilers.
@ February 14, 2014 11:04 PM in 007 CAPguess a 100 watt light bulb and a keyless bulb holder. Riello allows this to be used as a capacitor on their burners in a pinch.
@ February 13, 2014 8:21 PM in New furnace started kicking after a season of quietpiping is not right. No equalizer....hence the water level in the glass is all over the place. And maybe the reason the water hammer.
@ February 13, 2014 7:42 PM in New furnace started kicking after a season of quietpiping is wrong then raising the water level will throw wet steam into the main and cause water hammer. Do you have any pictures?
@ February 13, 2014 6:56 PM in New furnace started kicking after a season of quietBoiler is hammering. Adding treatments to the boiler water as a general rule will not help. Skimming is the best treatment. Get any oils out of it that are in there.
@ February 13, 2014 6:51 PM in 2# gas line for 600, 000 BTU'sFine. Run the 2# line from the meter. the regulator will have a red dot on it for a 2# set up.
Once you get into the boiler room hook it into a Maxitrol 325-7A
Then pipe out to each appliance as if the meter were right there.
@ February 12, 2014 9:52 PM in Radiators Hissing and steaming after insulation appliedYou just need to go the next step. The boiler is running on low pressure , its safe. If you want to quiet the radiator then twist the air vent shut or flip it upside down. Did you check the find a contractor listing?
@ February 12, 2014 9:03 PM in Radiators Hissing and steaming after insulation appliedyou need to either add some main vents in the basement or replace them.
They are larger than the radiator vents. Usually they are found at the end of the mains. Where are you located?
@ February 12, 2014 6:43 PM in Cold dayDo the primary loop w/ a 15-58 Then install another one on the primary loop. The primary should be full size. the piping off the main loop should be 1 pipe size less that 1/2 of the main. so if the main loop is 2" your piping off the primary loop should be 3/4"
@ February 11, 2014 9:43 PM in biasi b-3If you did the heatloss and your hot water needs are not crazy.
@ February 11, 2014 7:25 AM in I don't like my new boiler! oh noboiler w/ a Riello burner. Its not that bad. Riellos do have a unique sound...What is the model of Buderus boiler? 115? 215?. Now before having the entire boiler removed you may want to see if a Carlin burner can be put on instead. (it would depend on the boiler model) It may help.
@ February 9, 2014 6:24 PM in Biasi boiler review?when people bomb throw here and then never respond to other willing to help fix a problem...