Joined on September 3, 2009
Last Post on July 26, 2014
@ March 18, 2011 11:24 PM in Buderus rumbling and draft problem?your chimney? If it is a cold outside chimney it might be that it was cold and had poor draft.
@ March 13, 2011 4:18 PM in EZ Water....http://www.easywater.com/
No salt to add...
@ March 13, 2011 1:15 PM in EZ Water....Hi All.
I am inquiring to see if anyone out there has experience w/ the EZ water treatment system that it all the advertising rage on talk radio. Does it do what it says? I have a friend w/ poor water(hardness) that has had a softener for years now but the salt needed to get it to run right is killing the pipes and equipment. Water tastes terrible. water treatment co. says it is working right but IDK.
So before I spend that kind of money i am throwing it out there. What say ye!
@ March 12, 2011 11:31 AM in X-TROLL TANKbest way to know... and I should do this all the time but I don't is to break out the tire pressure gauge and check.... ya never know! kpc
@ March 11, 2011 5:54 PM in Converting oil burner to propanebut LP is prob. not a good option.... couple reasons. If you install a conversion burner you gen speaking lose 2% afue.... LP gas per gallon is abut 91,000 btu / gallon.... #2 Oil is 139,000 btu / gallon. figure out what your price per gallon of each is and you most likely will see that oil is a better price. NOW if it is Nat. gas that may well be a diff. story....
@ March 7, 2011 5:35 PM in used potable water pex in a heating loopon how much tubing is exposed, how hot the water is and how much steel/iron components there are. The more of each the higher your chances for issues. You can add oxyen scavengers on a regular basis... Rohmar comes to mind.
@ March 3, 2011 5:38 PM in Asbestos in burner chamber?asbestos. It is a ceramic fiber. Still it is not stuff to mess around with a lot..... depaening on how much fell out you are most likely ok. That is a dry base boiler. kpc
@ March 1, 2011 10:12 AM in Radiator banginglike the boiler is not properly piped...specifically near boiler piping. Could also be oil in the system... but we would need pict. of the set to confirm. break out the digital camera.
@ February 28, 2011 12:17 AM in Condensing Boilers and 2PSI Gasalthough I just did a pretty large 2 psi sysste, w/ 4- 200k FHA furnaces, 1- 380k Noritz, and a bunch of commercial kitchen stuff... I used a Maxitrol 325-7L on the tankless. I ran 3/4" black to the regulator then 1" out to the tankless. It works fine. It was pointed out to me that you should have a fair amount of pipe down stream from where you come out of the regulator ....say 15'-20'. Is this NAT or LP?
@ February 27, 2011 8:36 PM in banging pipes that wake the dead - please help!they installed the zone valves. Either they installed them backwards and/or they ahve them too close to the cirulator. Whaen both are open and one closes you get a problem called hydraulic jump. You could move the zone valves to the opposite side or installa diff. circulator... a grundfos 15-55 alpha would be ideal.
@ February 24, 2011 10:45 AM in Veggie oil.... in oil....?Here in NH I am hearing of problems w/ soot and Coke buildup on turbulators as a rumor of oil quality issues. Suposedly there was am issue w/ Peanut or veggie ol,that was not food grade and it was added straight to the oil mix at the regional depot... (not as Bio fuel) now there are these issues poping up all over So. NH and Maine.... adding 4in1 Hot or FuelRite does not help) Anyone heard of this happening elsewhere? kpc
@ February 23, 2011 5:32 PM in My burner has no expansion tank?systems w/ conventional expabsion tank should NOT have air vents in them. I see TWO in your 2nd pix. Close those off. This could be part of the reason you lost the charge in the tank.... kpc
@ February 23, 2011 4:35 PM in why is this?they like copper tubing... makes no sense to me. Not needed. kpc
@ February 19, 2011 10:58 PM in heating new cottage qith cathedral ceilingsefficency prob. about the same... Comfort... w/o a doubt Radiant. Practical... well it depends You can do 2 for 1 w/ a furnace. but what will get the most use. Heat or A/C...? How many cooling days do you have in Quebec? You probably can do a built in unit or a Mini-split. a/c unit w/o running duct work.
@ February 19, 2011 8:01 AM in heating new cottage qith cathedral ceilingsif money is not an object I would be doing radiant floor w/ Warmboard. This requires some fore thought as the 1" plywood needs to be used to frame up the structure. To say that no matter what you use means that the heat will rise is a misnomer. Radiant floor heat will not produce hot air thus the floor will be warm and the air at the ceiling will be cooler. Using hot air that will not be that case. There are electric boilers on the market.
@ February 17, 2011 7:46 AM in zone valve and boilermatewould any tstat. Taco, Honeywell or which type?
@ February 15, 2011 6:16 PM in A blast from the (no too distant) past...Just in case you ever wanted one of these you can get one cheap....
@ February 15, 2011 7:57 AM in Roll out switch failurewas installed was it sized properly? Did you do it or was it another company? Had a problem posted here a month ago where a sub contractor pulled the wrong liner down the chimney and that was the issue.
@ February 14, 2011 4:49 PM in Solia boiler not heating upcheck out the thread title "over sized boiler-dry fired" That is how you need to pipe your set up. Note the primary loop and the closely spaced tees that separate the boiler from the system.
@ February 13, 2011 5:23 PM in pre warming oiluse this for your DHW as I have. http://www.gfxtechnology.com/
@ February 13, 2011 8:28 AM in Burnham boiler making rattling noisetankless coil inside? I have has that happen to some boilers where the coil rattles during operation....kpc