Joined on September 3, 2009
Last Post on July 26, 2014
@ February 13, 2011 8:25 AM in pre warming oilhttp://www.westwoodproducts.com/tigerloop_article.htm
What A tiger loop does as it primary function. Because it has a small reserve of oil near the boiler it additionally warms it up. The waste water thing prbably will not warm up the oil enough to make it worth the effort. You would be best served to move the oil tank to a warmer room or create some place for it to be warm.
@ February 12, 2011 8:38 AM in pre warming oila Tiger loop will help. Cold oil is not the best thing. If your burner does not alrady have one a nozzle heater would also help. Is there a way to build a foam "house" around the oil tank and put 100W incadesent light bulb under the tank to warm it?
@ February 11, 2011 10:27 PM in Nice rad for sale in western massin maine... not far from Ken. Plenty rare.
@ February 11, 2011 6:54 PM in Primary piping outdoor non-pressurized boilerreally needed here. Seems the wood boiler should be going through the flat plate/ HX and if its a non press / open set up you need a high head bronze/ SS circ....
@ February 11, 2011 7:28 AM in How Can I, Suggestions Welcomeis to use a pex drop ear 90 and run barrier pex from the near boiler piping to a location out of the way. I prefer the 3 eared ones so that is has some beef to it. kpc
@ February 11, 2011 7:23 AM in can an incorrect system fill blow an expansion tank?now there may have been a defective tank. but filing the system....no.
@ February 10, 2011 5:46 PM in Solia boiler not heating uptwo pumps. One for the system and the other for the boiler. Also I would have the system one contolled by the t-stat and the end switch off that go to the boiler control which in my opinion should be a tankless boiler aquastst. That way the boiler is not prolonged in condensing mode.
@ February 9, 2011 4:10 PM in Solia boiler not heating upthe one circulator? I can't really see that well as to what goes where.
@ February 8, 2011 12:03 PM in Lack of heatHave for a Hot water system? Kind of soulds like a tankless coil... Sounds like it is "Limed up" and is not transfering heat well. Either replace the coil or do an acid wash to get all the crud out. How hard is your water? A long term solution needs to deal w/ that....kpc
@ February 8, 2011 7:17 AM in Need help with sq ft of steam radiatorsai the 1st rad columns or tubes?... how wide is each.?
@ February 7, 2011 10:22 PM in failed diaphram expansion tankpossibility it was on the way out. You probably just put it over the edge. Too bad you have a customer like that.... might be time to tell them to find someone else.
@ February 6, 2011 8:46 AM in Solia boiler not heating upfew pictures to see what you have for piping. Sounds like it is a HIGH mass system and a LOW mass boiler. Not a real perfect match. However it may be fixed w/ a proper piping strategy and some appropriate controls. Running the boiler below 140 is not a good longterm idea.
@ January 30, 2011 8:15 AM in Buderus panel noiseall the air out w/ the system pressure @ 18 psi....? IF the air keeps showeingup I would suspect the air seperator is not working and or your piping is not the best for air removal...what is your system like?
@ January 27, 2011 10:06 PM in Stainless Flue Pipehave for a boiler/ furnace ? Oil or Gas? power vented or chimney vent? kpc
@ January 21, 2011 8:02 AM in 2nd water heater installationis run the water through the coil. Then run the hot water from the coil into the cold of the tank water heater then out the hot water side to your fixtures. Wire the electric heater as if it were all by itself. (make sure it is full before energizing) This will temper the cold water to keep the operating costs down w/ the electric yet the electric will give them a head start.
@ January 20, 2011 5:03 PM in Steam stumper...I will keep at it. The big rad in the living room is a bit better w/ the varivalve.
@ January 19, 2011 11:40 PM in Steam stumper...1 pipe , paralell pipe. Near boiler piping is ok. 1 bull head tee but not real bad. 2 Gorton #1 on each main. the old ones were plugged. Rad vents are various. some gorton D upstairs. the problem floor has 1 varivalve, 1 ventrite. edr is around 500 ft2.
@ January 19, 2011 10:22 PM in Steam stumper...Looked at a 3 unit apt today... 1 each floor. 1 steam boiler. T-stat in the bottom unit. strange oddity is that the 1st floor apt does not get heat ... all 4 rads cold but the risers to the 2nd and 3rd are piping hot. I replaced the main vents a while back and can hear them panting. I have a varivalve in the back bathroom rad and still no change.... strange thing is that the riser to the 2nd and 3rd floor and just inches away from the 1st floor rads.. all piping is insulated. ty,kpc
@ January 18, 2011 7:53 AM in valves used in hydronic boiler systemsresidential situations a ball valve is fine. Gate valves should never be used to throttle.... that will wear them out in no time.
@ January 17, 2011 11:49 PM in PIPES KNOCKINGa number of things. Too high a water temp., too little pressure, air in the lines, improper piping or expansion noise from the pipes rubbing up along the wood....kpc
@ January 17, 2011 7:42 AM in Removing air valves in one pipe systemmay very well run into is that the steam will "pour" out into the room. This will not condence and return to the boiler. You could end up w/ adding water to the boiler where you did not have to. Also steam could very well burn an unsuspecting person.