Joined on December 16, 2009
Last Post on March 7, 2014
@ January 23, 2014 7:44 PM in Copper Riser Piping and SupportI like kindorf and kindorf clamps.a?though and no offense intended if you are unsure how to support your pipe or which kind of copper to use why not call a plumber.again firewatch is important if you are uncertain.good luck
@ December 15, 2013 7:39 PM in pipe sleevesI always sleeved my pipe with steel pipe when going through weight bearing walls etc and this is how i was taught,2 pipe sizes larger.That was in nyc. Now working on long island and all I see is pvc sleeves .which practice is right?
@ December 8, 2013 10:28 AM in flow check valvestried it on my own system and will never look back.
@ December 8, 2013 10:24 AM in Copper Press FittingsI was beginning to give up hope.There is a lot of heavy hitters here advocating press fittings.You got a tough fight on your hands .
@ December 5, 2013 7:11 AM in 1/2" pex homerun to iron radsi use this system a lot,works just fine
@ December 5, 2013 7:07 AM in Navien ch 240did you check gas pressure,minimum 7" wc,full port ball valve on gas line etc.I had a call last week and that was the problem but if your getting a new unit im sure all that has been checked,good luck
@ December 4, 2013 9:09 PM in pex and homerunswhen I took a class the inspector said pex could only be used if using a homerun system,i am talking about domestic water.Now all I see is pex with fittings cut in similar to a copper install.When you look at the inside of a 3/4 pex 90 it is similar to a 1/2 copper fitting.Is there a significant pressure drop if you dont use a homerun.I would rather use copper but its getting harder to compete with pex prices.Thanks
@ December 4, 2013 9:02 PM in NTI Trinity FTFInstalled my first one two weeks ago and was impressed especially with control board.No issues with start up and customer is very happy.Good luck with it,i would take an IBC over it though but a fine boiler.
@ December 1, 2013 10:42 AM in radiant and wood floorI used heat transfer plates before (uponor) on a job with no problems.I use a heating consultant on every job,I know my limitations,he sizes pumps etc and I put it together.
BTW I enjoyed your steam boiler pics that you posted before,reminds me of a guy I used to work with.Take care and thanks for your response.
@ December 1, 2013 8:40 AM in radiant and wood floorwhere are homeowners getting their info that it is a no-no.So far I have givin 4 of dans book on radiant to homeowners(yet to be returned).Next year im doing staple up in my own house(funds permitting)and my wife has already said if the floor buckles the result wont be nice.I actually came from a job yesterday,radiant heat no mix and 170 degree water going to floor.Ouch.
@ December 1, 2013 8:34 AM in LwcoI know on steam they require it .On hot water high limit is required not sure about 2nd lwco
@ December 1, 2013 8:31 AM in cut my bill by 70%,Thanks Rod for your helpI just converted .My old oil fired boiler was running me $460 p/m 12 months a year.Had a renovation done to house a few years back but typical Long Island renovation(everything bare minimum).Got in touch with a hydronic designer and we went over my situation.He did blower door test etc and we didnt do to good but minor stuff which can be fixed.Anyhow I used to be a pumpaholic until he turned me onto Caleffi.We used an IBC moulating boiler ,indirect I went with an Alliance(long island water)a couple of guys here advised me on this.I have had a lot of success with this indirect in the past.Grundfoss 2699 on indirect,1558 on primary loop and grundfoss alpha with caleffi zone valves.Rod you gave me info on my recirc line which I used and apreciate your advice.Bottom line gas bill $140.I love this new set up with intelligent pumping etc and in the future will be using it.Before I would pump on every zone etc but Im loving this set up.What beautiful products caleffi makes from their zone valves to their DHW mixing valve.Thanks to Dominic from ABCO for designing and comisioning boiler.
Producing 4-5 gallons of condensate a day.Wife was very happy with bill as oil bill was hurting.Thanks guys.
@ November 28, 2013 9:20 AM in sandy revisitedThanks for explaining that to me.So how did Fema pick and choose as to who were doing the installs.Was there a special criteria to get on there list.I am talking mainly about private work that was done but have come across a block in the rockaways that was done by rapid repair which we are going to repipe a few boilers.Thanks for the clarification
@ November 28, 2013 7:37 AM in sandy revisitedBrian,I understand where you are coming from but I had 2 baxi repairs.they combined 3 zones into 1 and used internal circulator and no p/s.Not complicated but I hate to think they screwed these jobs up intentionally.I finished a PVG install last night.A local licensed plumber did the work.3/4 pex to indirect and all pex piping on boiler,also no mixing valve on radiant.I am not sure John about naming names here but the company you mentioned are certainly guilty.Rich,I will email you later,I think your suggestion is very good.Happy Thanksgiving all.
@ November 27, 2013 7:21 AM in sandy revisitedHi all.So we are a few weeks into heating season.So far I have had to repipe four boilers that were installed by a large company that came to everyones rescue(and not at a cheap price).I know the situation was hard ,getting boilers,parts etc but what I am seeing is a complete disregard for the victims.A question to all you get rich quick plumbers,why not answer the peoples calls come back and do the right thing.
@ November 11, 2013 7:00 AM in burnham ES2 pilot assemblyAnyone from Burnham out there.With such a high failure rate on the pilot assembly how does quality control let this pass.Such a shame as this boiler fits so many customers needs.
@ October 14, 2013 9:01 AM in recirc lineI forgot to mention there will be a pump on the recirc line
@ October 14, 2013 8:50 AM in recirc lineyeah i am using a mixing valve on outlet and storing water at 140. Burnham Alliance doesnt show a piping diagram for a recirc line.I saw on a taco drawing about bringing it into the bottom of indirect.Actually my first time using caleffi material and what quality they have.I will post pics after install.Thanks again.
@ October 13, 2013 9:03 PM in recirc linehow do you guys prefer to pipe in a recirc line into a indirect without a designated port.
...into bottom of tank(remove drain and install tee etc) or into cold water supply with check.thanks
@ October 11, 2013 7:29 AM in New Furnace Setup - What do you think?fail,,,if counted a few times he failed it,thats enough for me.fail is fail no guess work.call installer hopefully he will do right
@ October 11, 2013 7:25 AM in The best pipe dope.teflon and pro dope.on gas only pro dope=no problems.me and bluebloc dont get on to well,i get more on myself than the pipe...good thread
@ October 9, 2013 7:03 AM in Looking for a decent boiler w/ indirectI have had luck with Burnham ES2 and an Alliance indirect.Install an outdoor reset and I really think you got a competitive system unless you go for more advanced boilers such as stated above.