Joined on February 27, 2010
Last Post on April 20, 2014
@ March 29, 2014 7:48 PM in Help! I have no main vents! + problem radiatorThanks for participating on The Wall!
Agreed that those vent locations look good. I would use a Gorton 2 for every 20 feet of 2" main. Try to get the steam main full in about 5 minutes. You could also add on a Vaporstat in conjuction with the new venting to run at super low pressures. Low pressure = low fuel usage.
@ March 26, 2014 7:14 PM in Northeastern PaI travel anywhere for steam. Get in touch and maybe we can offer our services.
@ March 24, 2014 7:48 AM in Adding cast iron baseboard to one-pipe steam systemI would use an 1-1/4" angled valve with a reducer on the spud. This will allow the water to drain freely from the BB and give you the benefit of a bigger sized valve to allow steam and condensate to live happily together.
@ March 23, 2014 5:27 PM in adding Walls around Boiler50ft3 for every 1,000 BTUH if the room is going to be sealed. And please leave 24-36" or more around the entire boiler. Make a door that is big enough to remove the boiler in the future.
@ March 23, 2014 5:26 PM in i got to get rid of this steam heat system, i got questionsYou might as well drive the dagger right into our hearts.
Why don't you like the steam system?
@ March 23, 2014 8:36 AM in 2 Pipe system - water hammer on one radiatorI'm going to guess that the bathroom was remodeled at some point. That's usually when bad things happen to good steam systems. Sounds like there is some improper piping in the floor.
@ March 22, 2014 10:48 PM in Adding cast iron baseboard to one-pipe steam systemI guess it would only work if the air vent was in the dead center of the BB.
@ March 22, 2014 8:26 PM in Adding cast iron baseboard to one-pipe steam systemI've always wondered what would happen if you piped it like a two-pipe BB but had the return tie back into the supply riser. Never tried it. Seems like, at the very least, you would create two supplies to handle the condensate that just one 3/4" supply might not tolerate.
@ March 22, 2014 8:22 PM in Main VentsI used to work with a plumber who would install vents on the near boiler piping because it made the water line more stable. What he didn't say publicly was that his waterlines were incredibly unstable because of his horrible piping practices.
I'll bet that once the vent is plugged, you'll see a disappearing waterline or some other quirk. The vent is not a good answer to the problem, but a very good mask.
@ March 21, 2014 11:00 AM in Weil-McLain & Caleffi InstallationIf somebody took the insulation off, would the solder joints still look perfect as always?
@ March 17, 2014 8:03 PM in WANTED: Asbestos Removal Co. in NJThanks, Victor.
Ice, I'm looking for direct referrals. We do work for an energy audit company and would like to recommend a company that somebody has used before with positive feedback.
@ March 17, 2014 5:30 PM in WANTED: Asbestos Removal Co. in NJAny reccomendations?
@ March 9, 2014 10:06 AM in Beating a dead horse.I don't trust the 82% rating either.
All I know is from what I see in the field. Atmospheric boilers need just as many adjustments as a power burner. I've almost never fired up an atmospheric boiler and walked away without making adjustments. The excess air and O2% are always way high, and combustion efficiency is way low. And should we even get started on the horrible engineering behind draft hoods? I've seen draft hoods allow massive backdraft without shutting down on safety. Never seen that with a draft control and safety switch.
I do agree that the most important factor with any boiler is the installation and set-up. We install both wet-based and atmospheric boilers. We all see some horrible work being done by other "experts". Incompetency and ignorance in this field will never go away. All I can do is offer the best solution possible, and not worry about catering to "the next guy". I also completely inform my customers about the future possibilities of needing service from a company other than my own. 90% of them don't see it as an issue. It may be naive, but I have to operate my business as if I will be around forever. I should be the only company servicing my installs for their entire life.
@ March 9, 2014 9:34 AM in Beating a dead horse.So how do you convince a homeowner to remove an 85%+ boiler with a power burner, and install an 82% atmospheric boiler?
Atmospheric boilers are set up on the whim of the factory assembler. Who do you trust more, your own technician with an analyzer, or a production-line worker with a pneumatic drill?
If Harper actually works for Burnham, then all he is convincing me to do is to never buy Burnham. This is a very distrubingly sneaky tactic, to come on here and peddle their products. Maybe a phone call to US BOILER will confirm his affiliation?
@ March 8, 2014 8:36 AM in For all you steam heads out there"You can't fix stupid". But, you sure can record it.
@ March 8, 2014 6:35 AM in For all you steam heads out thereFunny...they didn't leave the option for comments.
@ March 5, 2014 6:15 AM in Help needed on flame rollout switch keeping trippingCould be a leaking gas control valve. It's supposed to shut off completely. Maybe it's allowing a little bit of gas through upon closing. Do you smell gas after it's off?
@ March 4, 2014 8:05 PM in question on dry returnsFor two-pipe, either way is acceptable. No steam will be in the returns to create an imbalance.
@ March 2, 2014 8:44 AM in A challenge...Apparently CARLIN has a H2L two-stage oil burner that is only being shipped on certain furnaces. I THINK the main controller changes the motor frequency to deliver less gas/air on low fire.
One would almost want to find this control and adapt it for use on ALL burners. Hmmmmm...maybe "somebody" is working on this, and may have some test data to offer in the near future.
@ March 2, 2014 8:36 AM in Beating a dead horse.Please keep Mark's name ahead of mine. He is the mastermind behind the EcoSteam modulating boiler, I just tightened a couple of bolts and stuck a probe in the stack.
@ March 2, 2014 8:32 AM in RadiatorsWhere are you located? If you are dead-set on getting rid of the old radiators, I will take them from you. Do not send them to a junkyard, please!