Joined on February 27, 2010
Last Post on July 29, 2014
@ April 17, 2014 9:45 PM in Twin Steam Boilers - 4 Stages of Firing RatesThe old boiler was a 5 section 78 series Weil McLain oil boiler. It was about 30 years old and leaking from every single section.
@ April 17, 2014 9:33 PM in Twin Steam Boilers - 4 Stages of Firing Rateshttp://s3.supplyhouse.com/manuals/1265283159157/25260_PROD_FILE.pdf
I'm really liking this valve. It has a pilot valve, so it only works with intermittent pilot, but eliminates the need for a separate pilot control. The small size is 300,000 with 3/4" tappings. And, it's a step open valve. Big advantage.
@ April 17, 2014 9:11 PM in Twin Steam Boilers - 4 Stages of Firing RatesOh, and over the summer, we'll be installing MarkS's EcoSteam control on this system. I figured...why not add ONE more control to confuse the next guy in 30 years.
@ April 17, 2014 9:06 PM in Twin Steam Boilers - 4 Stages of Firing RatesSo, we just wrapped up another twin boiler setup on a Warren/Webster vapor system. Oil to gas conversion. Since the SMITH 8 is no longer in production, we've been installing a lot of PEERLESS 63 series boilers. The only way we feel good about an atmospheric boiler is by installing a 2-stage gas control valve in them. Robertshaw makes a series 700 two-stage valve that comes in two different sizes up to 720,000 BTUH. Super easy to retrofit and install. The High is 100% and Low is 60%. It's the absolute perfect fit for High/Low on a steam system. As soon as the mains are hot, you can drop out your pick-up factor and run on Low fire until the t-stat is satisfied. On this job, we're controlling 4 separate firing rates. I can maintain 4-8 ounces of pressure with just the Low fire of one boiler.
We installed orifice plates in all of the rads/convectors, as well as upgraded 3 original WW crossover traps. The Air Eliminator check valve is still functional and maintaining a massive vacuum. It takes less than 5 minutes to get 50 feet of main hot.
Each boiler has its own 3" drop header that feeds a 5" system drop header. Dry steam is happy steam!
The picture quality is not great. One day, I'll get some better photos.
@ April 16, 2014 5:18 PM in Dunahm Air Eliminator replacement availableAwesome find! For that price, I'll try it on the next job. We would easily spend that much money on a bunch of Gorton #2's anyway. The only drawback is that it would not hold back steam if a few return traps went bad.
@ April 13, 2014 3:10 PM in Slab house/Boiler in kitchenNobody will know if it'll be okay until it's installed and properly tested. For me, trial and error is a bad way of installing systems. That boiler is capable of being top-vented. I would make a new hole in the chimney high enough to handle the right size draft control.
@ April 12, 2014 8:47 AM in Help with Sizing a BoilerI've been using a 15% piping factor for insulated mains with great success. But, not everyone is that daring! I would use an EG-45. Well, I wouldn't use a Weil McLain at all, but that is a different, and heated, topic altogether.
EDIT: Using a smaller boiler size will require the rest of the system to be in perfect operating condition; ie: better-than-recommended piping, massive main venting, correct radiator venting, and low pressures.
Just in case you wanted another opinion with a completely different model/size to muddle your decision...
@ April 5, 2014 6:46 AM in how should I prepare the system for summer?I like the idea of flooding the boiler. Nearly 75% of the leaking boilers we find are rotted out right at the waterline. I would rather replace a riser pipe than a boiler every 10 years. If you drain it completely, you'll have to add a dessicant inside the boiler or completely hand-dry the inside. Both options are impossible or implausible.
When you flood the boiler, let it run until it starts to make a terrible surging sound. That'll be hot enough to boil the O2 out.
@ April 4, 2014 3:26 PM in steam boiler maintenanceDon't drain the entire boiler, just a cup or two.
@ April 4, 2014 6:09 AM in Spewing air check! What to do?Can you post pictures of the boiler piping?
@ April 3, 2014 10:51 AM in Value of converting oil/steam to modcon gas?I messaged you privately about this. My BIGGEST pet peeve is a lack of communication and response. I'm guilty of it myself sometimes, but there's no excuse for completely breaking communication like that.
@ April 3, 2014 6:07 AM in Value of converting oil/steam to modcon gas?It's hard to reply to every thread here during the winter, as Steamhead has said. Sometimes, we can go weeks without spending much time here. Since I was in the original thread, I'm assuming that the comment was made about me.
Feel free to call or email me any time. I'm available 24 hours a day for emergencies, and generally open to a phone call at any time of day.
If you really want to rip the steam out, let me come by and take the radiators. They don't belong in a junkyard. We'll donate them to a proper steam system.
@ April 3, 2014 5:55 AM in Value of converting oil/steam to modcon gas?I wonder what they would say if they were talking to somebody else; somebody who didn't install the system. If they've enjoyed your service over the years, they may not want to say anything negative about the work. A lack of complaints is not the same as an approval. Then again, they may be telling the truth. Maybe steam isn't the best system for everyone. It's just that when I hear the same opinion from every single one of my customers, it becomes easier to believe that it is. Especially the ones who want to switch BACK to steam after it was ripped out.
@ April 3, 2014 5:42 AM in steam boiler maintenanceI recommend once a week at first. If the water is clean, go every two weeks, or 3 weeks, or 4. But, never less than once per month. The water should be tea-colored or slightly less than clear but never thick or gritty. You should drain the boiler as often as needed to keep it clean without having to add excessive fresh water.
@ April 2, 2014 8:49 AM in Value of converting oil/steam to modcon gas?Don't ask us contractors. We have our favorite systems, and our own agendas. Ask the homeowners who have converted from steam to something else. They'll tell you the real story. Higher fuel bills and less comfort. It would be foolish to remove the steam system.
@ March 31, 2014 8:29 PM in McDaniel #16 Steam trapUmmmm PICTURES PLEASE! We'd all love to see the setup, if it's all original.
@ March 29, 2014 7:48 PM in Help! I have no main vents! + problem radiatorThanks for participating on The Wall!
Agreed that those vent locations look good. I would use a Gorton 2 for every 20 feet of 2" main. Try to get the steam main full in about 5 minutes. You could also add on a Vaporstat in conjuction with the new venting to run at super low pressures. Low pressure = low fuel usage.
@ March 26, 2014 7:14 PM in Northeastern PaI travel anywhere for steam. Get in touch and maybe we can offer our services.
@ March 24, 2014 7:48 AM in Adding cast iron baseboard to one-pipe steam systemI would use an 1-1/4" angled valve with a reducer on the spud. This will allow the water to drain freely from the BB and give you the benefit of a bigger sized valve to allow steam and condensate to live happily together.
@ March 23, 2014 5:27 PM in adding Walls around Boiler50ft3 for every 1,000 BTUH if the room is going to be sealed. And please leave 24-36" or more around the entire boiler. Make a door that is big enough to remove the boiler in the future.
@ March 23, 2014 5:26 PM in i got to get rid of this steam heat system, i got questionsYou might as well drive the dagger right into our hearts.
Why don't you like the steam system?