Joined on February 27, 2010
Last Post on July 16, 2014
@ December 9, 2012 5:10 PM in A recent Smith / Carlin EZ-Gas installUsually, we only have access for one location or another. I like the horizontal tee because it saves an extra elbow,and allows us to inspect the chimney without taking anything apart. I've been able to control the draft very well with either location.
@ December 8, 2012 10:31 PM in A recent Smith / Carlin EZ-Gas installhttp://www.facebook.com/media/set/?set=a.415326681869913.92655.353747484694500&type=1
I'll skip trying to make the pictures upload correctly. We finished this job yesterday. At the end of a long day, we found that the gas supply was faulty from the utility service, so we never got a chance to run it. Hope to have the prolem fixed early next week. Will post some combustion results then.
@ December 4, 2012 10:45 PM in need a pipefitter in central NJ to build a new near-boiler setupWe're set up to do the work in two weeks. Will take plenty of pictures. And we'll get to sit down and work because the basement is only 5 feet tall. Was everybody a foot shorter in the 1800‘s?
@ December 4, 2012 7:45 PM in Condensate from chimmneyWhat size is the liner? How tall is the chimney?
@ December 3, 2012 7:53 PM in Conversion to Gas - two systems to one.Zoning steam is not as easy as throwing on a couple of valves. It has not been installed correctly and needs to be rectified.
Can you take more pictures from the front of the boiler?
@ December 3, 2012 7:50 PM in need a pipefitter in central NJ to build a new near-boiler setupI'm your man. Go through my info and call or email me.
@ December 2, 2012 3:57 PM in Utica steam and return pipesThat is...incorrect...inaccurate...umm....wrong.
Do you have pictures of the boiler and piping?
@ December 2, 2012 12:54 PM in water introduced to boiler???Well, it has to be coming from somewhere.
Sometimes, old valves can leak past, even if they are closed.
Is there any type of water coil in the boiler for domestic use?
@ December 2, 2012 7:43 AM in Utica steam and return pipesOld pipes leak. It happens. Closing radiators shouldn't have caused it. My only first reaction, if there are a lot of leaks, is that something may have triggered it.
What kind of maintenance has been done? Do you have an automatic water feeder?
@ November 30, 2012 9:28 PM in One-pipe steam with copper pipingI do work around Philly. I'd be happy to take a look at your system.
@ November 30, 2012 9:25 PM in Steam Boiler to Baseboard HeatThe pump also needs to be bronze or stainless steel with a bypass line installed to temper thr water.
@ November 29, 2012 4:07 PM in Steam Radiator RattlingI've had this same scenario happen. Th disc in the valve fell off and was flopping around inside whenever the steam came up.
@ November 27, 2012 10:53 PM in 2 Pipe Steam System - Water Hammer - No Trap - Some Side VentsI travel to all of NJ. Go through my company info and give me a call. We can set up an assessment meeting.
@ November 26, 2012 9:20 PM in 2 Pipe Steam System - Water Hammer - No Trap - Some Side VentsHoly crow! Where to begin?
You have a total cluster of bad piping and mismatched systems. Is only the one radiator not working well? Do you have a picture of that radiator and the piping that leads to it from the basement?
@ November 25, 2012 10:53 PM in Two furnaces, at same time, both lost heat but still blow cool airThat code is for ignition lockout. I would suspect a gas line shut down, but the water heater is working. My next thought is a common chimney or draft problem. Arethe furnaces sharing a chimney? Is there a valve on the gas line near the meter that only serves the furnaces?
@ November 25, 2012 6:29 PM in Another W-M SGO questionI forgot to take"after" pictures of the inside of the boiler.
@ November 24, 2012 7:32 PM in Smith Series 8 boiler - installed without draft control?Why do we install Temperature/Pressure relief valves? The boiler SHOULD never need one...
Why do we install roll out safeties? The boiler SHOULD never need one...
Why do we install draft control dampers?...
@ November 23, 2012 11:45 PM in Columbia Joins the Wet-Base Power-Gas Steamer RanksNice! I like how the header squares up the whole system. What were your combustion numbers with that model boiler? The Starfire usually gets around 82%.
@ November 23, 2012 11:42 PM in Oil to gas conversionIt can be converted depending on a few factors like furnace model, age, and condition. If it were mine, I'd go for a high efficiency replacement with staging or modulation for the best comfort and fuel savings.
@ November 22, 2012 8:32 PM in How much hot water heating can be added to steam boiler?Don't go more than the pickup factor of the boiler. That can be hard to judge, unless the boiler is sized correctly. Typically, it will be between 15-30% of the boiler's output.
@ November 22, 2012 8:29 PM in Converting to nat gas-a case studyWe came up with about 363 square feet of radiator load. The mains are mostly insulated, so I added 15% pickup, plus 15% for efficiency loss, and came up with a boiler input right near 120K. I believe the old 568 boiler is actually rated up to 210,000 BTUH. We see a lot of shocked faces when we go into a house, offering to install a boiler that is half the size of the old one. I mean, the old one worked, right? Yeah, and it could have also heated your neighbor's house. If I were in the business of selling fuel, I'd oversize my boilers, too. And then we talk about high 85-87% efficiency, and people don't believe it. Old habits die hard. Old steam habits die hard, come back, and haunt us for decades.
The installation will include the boiler, oversized drop header, Vaporstat, maxxed out main venting, and a whole house radiator vent upgrade. I can't wait to compare the annual fuel savings.
@ November 22, 2012 1:58 PM in Smith Series 8 boiler - installed without draft control?The draft control ensures that the boiler does not get TOO MUCH draft. It does not produce draft. High draft reduces efficiency. It may only cause problems when the weather gets colder, causing the draft to increase. Have it installed.
Banging is caused by improper pitch. Check the level of the main pipe.