Joined on February 27, 2010
Last Post on July 27, 2014
@ December 17, 2012 12:17 PM in Extremely Loud Banging in Pipes/Shaking FloorboardsIs this two pipe steam?
Banging is caused by steam and water meeting each other where they shouldn't. I'd suspect sagging pipes, or improper piping techniques.
@ December 16, 2012 5:21 PM in Cold radiatorHow does the supply run out look? Proper pitch? No sags?
@ December 16, 2012 4:49 PM in steam from tank ventAnd you still needt o maintain a proper height from the water line to the trap after the zone valves. 28" per 1psi.
@ December 16, 2012 2:27 PM in steam from tank ventI didn't realize this was one pipe steam. If the tank is staying, then as mentioned, all steam lineswill haveto be trapped. An easier solution...get rid of the tank.
@ December 16, 2012 10:06 AM in steam from tank ventIf all of the returns are joining below the water line, you shouldn't need to trap them all. Why is there even a condensate tank at all?
@ December 9, 2012 6:18 PM in Close to perfect BUT...banggggAnother thought.
The indirect tank does not have a tempering bypass. When he boiler is fully steaming, you may be flashing off inside the tank.
@ December 9, 2012 5:13 PM in Purpose of this pipe?Is there any marking on the outside? If not, how could it accurately be used for any type of inner channel?
@ December 9, 2012 5:10 PM in A recent Smith / Carlin EZ-Gas installUsually, we only have access for one location or another. I like the horizontal tee because it saves an extra elbow,and allows us to inspect the chimney without taking anything apart. I've been able to control the draft very well with either location.
@ December 8, 2012 10:31 PM in A recent Smith / Carlin EZ-Gas installhttp://www.facebook.com/media/set/?set=a.415326681869913.92655.353747484694500&type=1
I'll skip trying to make the pictures upload correctly. We finished this job yesterday. At the end of a long day, we found that the gas supply was faulty from the utility service, so we never got a chance to run it. Hope to have the prolem fixed early next week. Will post some combustion results then.
@ December 4, 2012 10:45 PM in need a pipefitter in central NJ to build a new near-boiler setupWe're set up to do the work in two weeks. Will take plenty of pictures. And we'll get to sit down and work because the basement is only 5 feet tall. Was everybody a foot shorter in the 1800‘s?
@ December 4, 2012 7:45 PM in Condensate from chimmneyWhat size is the liner? How tall is the chimney?
@ December 3, 2012 7:53 PM in Conversion to Gas - two systems to one.Zoning steam is not as easy as throwing on a couple of valves. It has not been installed correctly and needs to be rectified.
Can you take more pictures from the front of the boiler?
@ December 3, 2012 7:50 PM in need a pipefitter in central NJ to build a new near-boiler setupI'm your man. Go through my info and call or email me.
@ December 2, 2012 3:57 PM in Utica steam and return pipesThat is...incorrect...inaccurate...umm....wrong.
Do you have pictures of the boiler and piping?
@ December 2, 2012 12:54 PM in water introduced to boiler???Well, it has to be coming from somewhere.
Sometimes, old valves can leak past, even if they are closed.
Is there any type of water coil in the boiler for domestic use?
@ December 2, 2012 7:43 AM in Utica steam and return pipesOld pipes leak. It happens. Closing radiators shouldn't have caused it. My only first reaction, if there are a lot of leaks, is that something may have triggered it.
What kind of maintenance has been done? Do you have an automatic water feeder?
@ November 30, 2012 9:28 PM in One-pipe steam with copper pipingI do work around Philly. I'd be happy to take a look at your system.
@ November 30, 2012 9:25 PM in Steam Boiler to Baseboard HeatThe pump also needs to be bronze or stainless steel with a bypass line installed to temper thr water.
@ November 29, 2012 4:07 PM in Steam Radiator RattlingI've had this same scenario happen. Th disc in the valve fell off and was flopping around inside whenever the steam came up.
@ November 27, 2012 10:53 PM in 2 Pipe Steam System - Water Hammer - No Trap - Some Side VentsI travel to all of NJ. Go through my company info and give me a call. We can set up an assessment meeting.