Joined on September 1, 2010
Last Post on March 8, 2014
@ March 8, 2014 4:32 PM in 4-zone hydronic radiant heating systemA radiant floor can become air bound and can be difficult to purge if you don't have manifolds with flow setters and purge valves. Baseboard radiators can become air bound too but generally don't require as much apperatus, especially if they're looped in series like most are.
So, do you have baseboard rads or radiant floors, or both?
@ March 8, 2014 4:16 PM in What is this?It's a convector. Could be one of several brands.
@ March 6, 2014 5:28 PM in 4-zone hydronic radiant heating systemWhat type of emitters do you have? Baseboard, in floor, staple up, slab?
Not sensitive about the tankless, just tired of seeing people being ripped off by hacks and Internet peddlers. This topic comes up every week on here. There's a long post from last week on the "main wall" that's entitled "How Prevalent is This" that's deals with this.
@ March 6, 2014 11:04 AM in 4-zone hydronic radiant heating systemBecause it's a DOMESTIC water heater, not a boiler.
It is not designed, controlled or approved for space heating and probably now has no warranty because of its mis-application. It probably won't last 3-5 years.
At the moment, I don't have the time or the inclination to go into a long dissertation on the particulars of why its wrong; I've done that in several other posts and so have others here. You can search the site and find them.
A little bit of common sense: if a tankless water heater could take the place of a boiler, there would be no need to make boilers.
The decision to use a tankless is driven by two things:
First, the amount of mis-information dissimenated mainly through Internet peddlers and hacks.
Secondly, man's nature to try a get something for nothing or less than what it's worth.
The first preys upon the second and finds more than an ample number of recipients for its wares. These folks sooner or later come to realize that the laws of physics will out-weigh the laws of economics - every time.
@ March 6, 2014 9:54 AM in 4-zone hydronic radiant heating systemThat's definitely the wrong appliance for space heating. It's designed, controlled and approved for domestic water heating. It appears there's a second one to the left. Is that connected with this one?
If this unit is tied to both your domestic and space heating, you have the potential for serious health and system issues. Not the least of which is Legionella.
The piping is so convoluted that I can't follow it from the pic, but if this is an open loop, that would account for the problems youre having.
I would suggest getting a REAL hydronics pro to look at what you've got, not the hack who did this.
@ March 6, 2014 1:12 AM in Burnham recall?Here's a link to the recall notice:
@ March 6, 2014 1:06 AM in 4-zone hydronic radiant heating systemIs your "heater" a boiler or an instantaneous water heater? If you're not sure, give us make and model.
Your drawing doesn't completely show where the pipes running upward go. How about some pics?
@ March 5, 2014 9:13 PM in New Boiler PipingsHave a competent tech check your manifold pressure and set it to the spec on the burner data plate.
@ March 4, 2014 9:07 PM in New Boiler PipingsYour boiler connection to the closely spaced Tees is reversed.
Are you planning on keeping your present boiler and piping? If so, I wouldn't re-pipe it.
Again, you can't go changing things on an overhead system by trying to combine modern hydronic techniques with that type of system. That's a common beginners mistake.
If you're gonna replace the piping and boiler, then that's another story and p/s piping may or may not be necessary depending upon the new boiler and method of system piping employed.
@ March 4, 2014 2:57 PM in BTU Radiator Output? (see attached photo)The height should either be 20" or 28".
At 20", the btu output would be 11,190; at 28", the output would be 11,745. These values are approximate as you did not give the make, but ratings are pretty standard for these. Any enclosure modifications could substantially effect the output.
@ March 4, 2014 11:25 AM in 4-zone hydronic radiant heating systemThe installer may have come to realize his error and correct it by removing the actuator.
@ March 4, 2014 11:14 AM in 4-zone hydronic radiant heating systemThe last valve with no actuator is actually the return?
@ March 4, 2014 9:41 AM in BTU Radiator Output? (see attached photo)What's the height of the enclosure?
@ March 4, 2014 9:20 AM in Perplexing radiant floor questionIf you have a clamp around amp meter (aka amprobe) you can measure the amp draw from one feeder wire and multiply that times the voltage to get the wattage. Then multiply that times 3.413 for the btu output.
It looks as though you're a little lean on heat cable and I doubt that the floor alone will keep up when the temp is this low.
What your tile guy did was obviously wrong. He could have left tile out of the damaged area until it was properly repaired. I'm glad he owned up to it. Hopefully, he'll repair your tile at no cost. That would be the right thing to do.
@ March 4, 2014 9:07 AM in Hydronic off new DHW for BasementYou do not want to connect a hydronic zone to a domestic water heater. You'll create a breeding ground for Legionella as well as many other issues.
If you want hydronic heat in the basement, look at installing a combi boiler of sufficient size with panel rads or baseboards. The combi has separate circuits for domestic and space heating.
@ March 3, 2014 5:10 PM in Help!! staple-up insulation foil mythWhat controls the supply temp to the floor? Is there any provision for boiler protection?
@ March 3, 2014 3:03 PM in Honeywell Zone Valve V8043 wiringYour comment doesn't make sense. The yellow leads ARE the motor leads and the red ARE the end switch. I'm talking about the actuator, not any system wiring.
@ March 3, 2014 2:04 PM in Honeywell Zone Valve V8043 wiringThe yellow leads power the motor. The red leads are the end switch.
@ March 3, 2014 1:54 PM in So many problems...would be grateful for any helpGo to the "Shop" tab above and then to the steam books.
For a home owner, I'd recommend that you get "We've Got Steam Heat" first. It's more home owner oriented. Or, you can get the four set package, but start with this one.
@ March 3, 2014 1:40 PM in What's wrong with this?I'm surprised he didn't connect it to the suction line. :)
@ March 3, 2014 10:37 AM in What's wrong with this?Goodman does it again selling to anyone over the internet! And before someone defends them by saying there's no warranty or they don't know who their distributors sell to, let me remind you they have the best warranty tracking service through Benchmark. No, they know, but they'll sacrifice their reputation (whatever it's is) to turn a dollar. They're not the only ones, either.
@ March 2, 2014 10:34 PM in Lochinvar Knight boiler problemsNever had a problem or heard of any such thing like you've been told.
You've tagged onto the end of an existing thread. In order to stay on topic, we don't do it that way around here. You should start this as a new thread if you want more responses.