Joined on January 26, 2011
Last Post on April 18, 2014
@ April 18, 2014 3:02 AM in Visio DrawingsTekmar has stencils for visio
@ April 17, 2014 2:18 AM in Proper Wiring Help NeededI didnt even look at that because i've never put low and line voltage in the same conduit.
@ April 16, 2014 11:16 AM in Proper Wiring Help Needed@ techman..Looks like those 2 wires are going to the end switch
@ April 9, 2014 3:58 PM in New Lead Free ball valvesIn 1067, when I took my Journeymen's exam......
No wonder you retired. :)
@ April 1, 2014 4:55 PM in Auto fill/back flow preventer. Is it necessary?Not at all.
1. Just make sure you put in a low water cutoff.
2. Make sure you disconnect the hose when you're done.
I assume you don't have running water to the shop, otherwise it's not that expensive to put in the auto fill/back flow. Make sure you buy a cap for the boiler drain. After a couple times over the years, it may leak after use.
@ March 21, 2014 11:22 AM in Use any oil provider?If you're in an area with plenty of oil dealers, call someone else. It's probably best to get a recommendation from a friend or neighbor. Some people like the more personal service of a small company, some think bigger is better (usually more expensive too).
Just remember if you switch companies and are on automatic delivery to call them immediately to cancel future deliveries and to avoid a possible spill.
@ March 16, 2014 10:35 AM in Has a sink hole ever tried to swallow up a boiler you service?I meant when the owners, or whoever doesn't think this is a problem, see the stress on the gas pipe alone...how are they not frightened into immediately fixing it. If you hear they fired it back up, I would call the building inspector and the fire marshal. Seems like a lot of gas has gone BOOM this winter....
@ March 15, 2014 4:57 PM in Has a sink hole ever tried to swallow up a boiler you service?Anyone concerned about the stress on the gas pipe, or the venting pulling loose?
@ March 8, 2014 10:23 PM in Is this fixable?Can you post some pics? It appears you may have some themosiphoning. You feel heat in the return piping. How far away from the boiler, following the pipes in the non calling zones, do the pipes feel hot? Besides checking all the wiring/components, you may need some flo-cheks.
On a general note, a hydronics pro to check the entire system may help with your inadequate heating complaints.
@ March 7, 2014 10:36 AM in Heat loss through rim joistI think you should move the tubing. You said it's an inch to an inch and a half away from the rim joist. That means the tubing is looping under the wall of the room above. It didn't need to be that close. I would bite the bullet (if you did it yourself), or have the contractor come back and properly install the tubing-ie, move it.
Depending on your floor covering, someone will drive a nail, or fish a wire down the wall from above thinking there's no way radiant tubing is under the wall, and hit it.
And you'll get to insulate your rim joist properly.
@ March 5, 2014 9:50 PM in Weil McClain Boiler QuestionJust wondering if the domestic hot water is set for priority.
@ February 27, 2014 4:35 PM in Back up boiler sizeNo matter what you go with, properly size it to do everything you need without the wood stove. It wont cost you more money. And you never know what could happen to the 'stove stoker' in the future, and you'll be glad you have some automatic heat.
@ February 25, 2014 10:04 PM in Has anyone ever heard of this?There's been no autopsy on the I joist? If I were guessing I would lean toward mechanical failure caused by:
1. Improperly drilled holes
2. Improper cross bridging or cross bridging removed.
3. Improper engineering.
If it were moisture related, I wouldn't blame the radiant unless it was leaking. It's pretty hard to get a clear idea of what happened during construction--not weather tight, things like that.
Plus you mentioned it was installed in August. Humid climate?
@ February 22, 2014 6:18 PM in BobStupidity.
Or maybe he didn't have a smaller nozzle and he lowered the pump pressure thinking it compensates.
Or he doesn't understand proper combustion and all its elements, especially draft. When he looks at the fire and lowers the pump pressure, it looks 'better' to him. Maybe poor draft or partially plugged heat exchanger (poor, lazy cleaning), has the flame impinging off the back and this is his remedy.
Either way, get a better guy if you can.
@ February 22, 2014 6:11 PM in Cleaning a boiler.Not for me. The deposits off the ceiling need to be cleaned, but the chamber itself is probably filling up with (as Icesailor says) kibbles and bits. This will affect how efficient your burner fires, and how clean it will run.
Got to open the combustion chamber. On an old boiler if it's going to be a nightmare (rusted/broken bolts), it will only be the first time. After that, every year it will be easy.
@ February 21, 2014 1:12 PM in weil mclain 68 questions, help pleaseHow is it preheating the domestic tank? If it's boiler water (doubt it, but you never know), then you'll have to valve it off or drain it, cut/cap pipes, re-bleed system, remove controls,etc.
Most likely it's from the domestic coil. You can close off the domestic water supply on hot and cold, cut and cap it. But there is still a control issue to figure out. A triple aquastat or an aquastat in the hot water heater was controlling this somehow.
Post a few pictures, just to make sure.
BTW, if you gonna start cutting pipes on a 768, I'd be thinking about a new, triple pass (if oil) boiler, a modern gas boiler. and an indirect
@ February 20, 2014 10:46 PM in changing a garber filter1. Wait until the tank is empty.
2. Soot vac trick. Wouldn't recommend trying this on your own the first couple of times.
I even hesitate to mention it because you should only try it with someone who has done it before.
The only other way if you get lucky would be a clogged oil line.
@ February 19, 2014 9:48 PM in Looking for book recommendations!That advice did not come from any expert. No expert foregoes a heat loss calc. No expert oversizes. There are many truly amazing experts here on this site. One of them wrote about 17 books :).
Siggy's book is good, but it won't give you all the answers you are looking for.
My best advice is to check this site for someone close to you, then check their posts to get a better feel for their expertise.
All the books & diagrams can't possibly account for your exact situation. A competent pro can answer these questions accurately, and quickly. You can buy a few hours of his/her time and end up with a complete blueprint--heat loss, piping diagram, list of materials.
@ February 19, 2014 5:24 PM in How to vent oilDumb dumb, dumb. No one gets arrested for fraud.
@ February 19, 2014 5:18 PM in Looking for book recommendations!But I don't think a 'book or two' is going to give you all the information you need. You would be better off taking advantage of a hydronics expert to design your system--from proper heat load/loss, piping, emitters, controls, equipment, etc.
They already know what works and what doesn't, and can provide you with many options you many not even be aware exist.
Then with a proper plan, you can install away...
@ February 19, 2014 5:13 PM in Seeking info on unusual stem for antique hot water radiatorhttp://stores.ebay.co.uk/Total-DIY/Radiator-Utility-Keys-/_i.html?_fsub=5409365015
@ February 17, 2014 4:28 PM in auto-feed on or off for boiler for hydronic baseboard heat ?Add the LWCO, close the valve to the water feed. If there is a leak, especially when you are not home, you will have a mess.
A boiler is a living, breathing (well maybe not living or breathing) beast (ok NOT a beast), that needs some TLC and more attention then a scorched air system.
I have the LWCO, and the feed valve closed. I also walk by my boiler every day, on the way out and when I get home, and glance at the boiler gauge and the display on the Tekmar boiler control.