Joined on January 26, 2011
Last Post on April 18, 2014
@ February 12, 2013 4:32 PM in Direct Vent 80% boilerWhat fuels are the boiler and the hot water heater burning?
Most likely, your chimney is failing, and even though you probably could line it, I wouldnt without a certified inspection with a recording camera. The problems you see in the attic, peeling, etc are a sure sign the mortar is long gone, with the chimney to eventually follow.
Go with the above recommendations and use the sidewall venter.
@ February 11, 2013 10:26 PM in Beckett cf500 burner smith a19 series boilerDraft? Excess air? Then I would check the delay valve & pump cut off, transformer, etc
@ February 11, 2013 10:15 PM in Beckett burner leaksCheck this with a plugged nozzle in the nozzle assembly, outside the burner, attached to the pump (watch out with the transformer opened)
@ February 10, 2013 5:20 PM in bad boiler installation?I feel bad for you. How do you get the aquastat cover off...or even the aquastat? And forget about removing the burner or swinging the boiler door for a cleaning. The only long term correct approach is either a different boiler that can fit in the space, or that boiler on a different place
@ February 6, 2013 9:44 PM in Slant/Fin Hydronic Explorer 2.0 Help NeededOn geometry. I have come across this too. I just break the odd shape rooms into rectangles and triangles, and do the math that way.
Do you have a specific problem your trying to solve?
@ January 20, 2013 5:53 PM in What controls this:Did you happen to see these 2 PDFs?
The Tekmar should be doing almost everything, especially the mixing valve. There's a tedious checkout you can do on the Tekmar ( it's in the manual) which may help.
Maybe the Tekmar just isn't set up correctly by the original installer, and the sensors are in the wrong spot. For multiple zones there should be another zone control wired properly to the Tekmar
One thing I noticed with the Tekmar, when you have boiler protection set, something odd (to me) happens with the mixing stations. To 'protect' the boiler it will close 4 way, or stops injection mixing--which its suppose to do. But it seems to, I can't explain it, come out of this in a way that doesn't seem logical, & causes performance problems. Maybe someone else experienced this and can explain it better.
Any chance you can scroll thru the Tekmar menu and post the settings?
@ January 13, 2013 6:22 PM in Are there 12 volt DC circulator pumps?Phil, but your scenario, marine batteries, battery minders, extension cords, going out to start a car, and let in run during a blizzard, etc. sounds like a lot for a 77 year old woman.
Unless your in an area where they are price gouging gens, I think you'd be surprised how cheap you can do it with propane ( you already have a tank). If it were me, I'd pay a little for the piece of mind.
Plus what if the power goes out for a week or longer.....
@ January 13, 2013 5:18 PM in Are there 12 volt DC circulator pumps?An automatic propane generator, wired with a transfer switch that will do just the things you need
@ January 13, 2013 5:07 PM in Short CycleWithout staring at it when it happened, my guess is that right as the aquastat called for the boiler to fire for one of the zones, the call for heat ended . Like I said, kinda hard to tell without looking at the entire system/controls
@ January 10, 2013 5:52 PM in steam boiler conversion from Oil to Natural Gas?I would call Carlin Combustion, ask for either tech support, or the rep for your area (hopefully its Bruce Graham). They'll tell you exactly what will work in your boiler, and recommend a competent installer
@ January 10, 2013 5:47 PM in Control/system wiring diagramshttp://www.firedragonent.com/
George has some great books on wiring, lots of pics
@ January 10, 2013 5:42 PM in Nest Thermostat Not Getting Powerto the carlin primary control? or to the aquastat? If aquastat, which one is on your boiler.
@ January 7, 2013 5:46 PM in new tankless coil questionAre you saying your boiler is firing 3 minutes, every 20 minutes, just to keep the boiler hot, for DHW?
Whats the boiler temp (on the gauge) when the boiler fires (assuming it's not calling for heat). Doesnt sound right. Are you sure theres no faucets dripping anywhere in the house?
In my opinion, the cheaper way would be with in indirect, but first determine why the boiler is running so much. Clock the water meter when nothing is 'on' to see if some cold water is running thru the coil. Also make sure your triple aquastat is working properly.
Icesailor has a pretty good system for hooking up a boiler to an existing water heater. If he doesnt respond Ill try to look up the thread.
@ January 6, 2013 9:19 PM in Riello pump pressureChecking the pump pressure in low fire or high fire?
@ December 10, 2012 10:07 PM in What Is This Tapping For?on to something. Is that a burn mark on the side of the jacket? I would at least pull the top off and look for signs of leakage. Hard to tell from pic what the tapping is for. Is it suppose to be for air vent/steel exp tank?
@ November 27, 2012 6:21 PM in Looking for a Columbia Boiler manual..Thanks for the info & help, Bill and Steamhead. This is more for my curiousity. I just want to try everything possible, and to be armed with some knowledge for some people more experienced. I'll take the time to get it to run the best its capable of. If it's a goner, its a goner.
It's actually heating the original portion of a mechanics garage. The rest is heated with more modern equipment. But he's a real good hard working dude, so I'm gonna give it a go.
@ November 26, 2012 10:56 PM in Looking for a Columbia Boiler manual..Was just looking for some guidance, maybe someone remembers this boiler? I've only been in this game for about 20 years, and its the first I ever seen.
There is a thumb nut. The only usable info on the plate is 1.25 gph. I'm going set some (some? lol) time aside and figure it out.
@ November 26, 2012 4:37 PM in Looking for a Columbia Boiler manual..You are correct sir........The burner doesnt appear to have an air gate, just oval holes completely around the housing that look like a Beckett universal mounting flange. The basic problem is it has way too much excess air 143%, causing low CO2 (6.6), and high CO in the flue pipe (no CO outside the boiler). It probably has been running like this for years, and I'm the first knucklehead who spent some time with it.....lol
@ November 26, 2012 4:24 PM in Oil Tank Insurance - Accidental release of petroleumabout the terms of the insurance.
1. Do they price based on age of the tank?
2. Can you get a discount if the tank is installed per their specifications?
3. Would they give you discount if you had a double walled tank, and an OSV?
I never offered the insurance because despite what it promises, I doubt it will pay off, and it's a headache to manage. The last thing I want to do is have to go to court with the homeowner saying, "you said the tank was ok".
If it were me, I would, if you could, go with #2 & #3, and forego the insurance.
@ November 26, 2012 4:18 PM in Looking for a Columbia Boiler manual..I posted this on the other sites...
Was wondering if anyone had a boiler manual for a.....get this...Columbia FT 30, with a Columbia burner on it. Yes it belongs in the scrap heap, but in the real world (the real broke world), I would like to get this to run as best as I can. Basically looking for some original specs, and then I'll go from there. Called Columbia, they offered their condolences :). Any help would be greatly appreciated.
@ November 17, 2012 7:41 PM in Heating helpFirst, where is the expansion tank?
What size boiler? How many BTU's?
What radiation and how much on each zone?
Size of circs?
How many BTUs are needed on each zone?
How is the system controlled?
But to save you some time and find a quicker solution would be to get a competent hydronics professional out there.
Take some pics
@ November 10, 2012 6:16 PM in mad dog here...need warm air furnace helpIs that it comes up as York/Coleman. Comes up more under Coleman