Joined on January 27, 2011
Last Post on September 2, 2014
@ May 6, 2012 9:27 PM in Help sizing new gas boilermany high efficiency boiler have a vent kits installed in chimney and allowing for venting trough the existing chimney, and no ss lining required. as per water quality, your heating system circulates same water, being treated with water conditioner like sentinel x100, it becomes completely harmless. Don't fall for 50 year old technology.
@ May 6, 2012 9:20 PM in gas gun on existing oil burner or new gas boilerHere we go again. This is not saving money. What you are going to do is just waste your money. Installing high efficiency system in your house is the best investment you can make. Improving your house comfort and lowering your bills is what you have to invest in. Think investment. And find sane, qualified contractor. Those large over sized cast iron radiators will allow for lower water temperature, and low velocity low resistance, very effective heating. your arrangement is ideal for high efficiency heating.
@ April 29, 2012 12:09 PM in Replace steam radiator system with high-velocity mini duct?Mini ducts high velocity in my opinion is not an option at all. Installing properly sized steam boiler along with properly insulated, vented and controlled steam system, is the most economical way. (look at one pipe steam system control valves from Danfos).
2nd option would be convert system to hydronic heat with mod con boiler, but it will be pretty expensive proposition.
@ April 26, 2012 10:32 PM in circulators burning out frequentlyif installer mounted cartridge type pumps vertically, and if there is spring loaded check valve on discharge, it traps air and can create situation with pump working with no flow.
@ April 22, 2012 7:18 PM in best high eff. gas boiler/ hot water heaterViessmann as a first choice, Slant Fin Bobcat with Combi Cat unit as a second (economy)
@ April 15, 2012 8:21 PM in Polaris used for radiant heating & domestic hot water.Steve , you are absolutely right in my opinion. Also i think plate heat exchanger is needed not for heating, but for domestic hot water. slant fin combi cat is just right for the job. Has build in circulator, activated by DHW flow sensor.
@ April 14, 2012 9:57 PM in gas line size? and how to determine size.help tim plzYes, i was referring to the original post.
@ April 14, 2012 9:54 PM in gas line size? and how to determine size.help tim plzIn NYC utility can run service to house and install house gas valve. this is where their jurisdiction ends.
@ April 14, 2012 2:56 PM in Not always mod/conTo do proper comparison, heating degree day method will be more accurate
@ April 14, 2012 12:22 AM in gas line size? and how to determine size.help tim plzhttp://www.engineeringtoolbox.com/natural-gas-pipe-sizing-d_826.html
are you a master plumber? if not, why are you working on gas lines not knowing basic gas rules?
@ April 10, 2012 6:15 PM in Any issues with this near boiler piping diagram?What Freewatt does , is supplying electricity for 1/2 price and heating and hot water for free most of the time. net metering applies here to the extent, that you do not want sell electricity back to utility, all you want is to keep electric meter around 0. during electrical consumption house gets electricity from Freewatt and grid, so meter rotates to positive direction, at night, when Freewatt generates more than house consumes, it send power back to grid, and meter rotates to negative direction, decreasing electrical meter reading.
@ April 10, 2012 8:04 AM in Any issues with this near boiler piping diagram?i do it the way it shown on the picture, If there dirt it goes down not to expansion tank . actually there is no flow in the pipe between exp tank and connection tee. it is dead end pipe.
Also, after flushing, chemical cleaning of the system and adding water conditioner, there is not much dirt left in the system.
@ April 9, 2012 10:51 PM in Any issues with this near boiler piping diagram?you do not need flow check on low mass boilers. especially on boiler side of LLH. Also i would move expansion tank to the bottom of low loss header.
@ April 8, 2012 2:54 PM in Little Brass Cup-shaped thing above expansion tank is leakingAlso, you must have straight piece of pipe with no connections at least 18" upstream of this brass thing, ( or to be exact, cast iron thing it is mounted on) to get laminar flow for good air removal.
@ April 8, 2012 2:09 PM in Little Brass Cup-shaped thing above expansion tank is leakingThis air removal device. I always leave red cap loose, or remove it at all. If it leaks, replace it.