Joined on January 27, 2011
Last Post on September 11, 2014
@ May 11, 2012 11:00 PM in Copper to steel/iron in a closed loop systemNo, i v never used TSP and do not have opinion on that matter.
@ May 11, 2012 10:46 PM in Copper to steel/iron in a closed loop systemSure i'v seen it . It really does not matter if system closed or open, because this is electro-chemical nature of corrosion, not presence of oxygen, i m posting picture of corrosion of job, done by another contractor 5 years ago.
@ May 10, 2012 7:29 PM in Treasurer-Condo Associ had done steam to FHW conversions, and savings were considerable, ( up to 80% fuel cost reductions) but of cause those steam systems were shot. Then again, restore steam system ( I done that too) also not a cheap thing. I got excellent results with TXV control and proper sizing of steam boiler and savings were unbelievable as well. The trick is in the contractor, not a system. Real professional can fix and set up any system and make it efficient, knucklehead can screw up any system
@ May 10, 2012 6:44 PM in Copper to steel/iron in a closed loop systemall ferrous to non ferrous connections must be done with brass fitting or brass nipple or brass valve and so on (always brass). Do not use dielectric unions, they are always leaking.
Using teflon as an insulator is a bad idea, because tread connection in a sense is welded connection, and joint seals when metal is pressed against metal with such a force than molecules diffusion starts to take place between joining surfaces. This is a reason why pro dope is the best pipe dope, it consists from oil (lubrication) and abrasive ( cleaning unevenness of surfaces to allow metals better contacting each other)
@ May 9, 2012 7:37 PM in Help sizing new gas boilerIf you need something with long term reliability, why not consider wooden stove? Just kidding. It is 2012 today.
@ May 6, 2012 9:27 PM in Help sizing new gas boilermany high efficiency boiler have a vent kits installed in chimney and allowing for venting trough the existing chimney, and no ss lining required. as per water quality, your heating system circulates same water, being treated with water conditioner like sentinel x100, it becomes completely harmless. Don't fall for 50 year old technology.
@ May 6, 2012 9:20 PM in gas gun on existing oil burner or new gas boilerHere we go again. This is not saving money. What you are going to do is just waste your money. Installing high efficiency system in your house is the best investment you can make. Improving your house comfort and lowering your bills is what you have to invest in. Think investment. And find sane, qualified contractor. Those large over sized cast iron radiators will allow for lower water temperature, and low velocity low resistance, very effective heating. your arrangement is ideal for high efficiency heating.
@ April 29, 2012 12:09 PM in Replace steam radiator system with high-velocity mini duct?Mini ducts high velocity in my opinion is not an option at all. Installing properly sized steam boiler along with properly insulated, vented and controlled steam system, is the most economical way. (look at one pipe steam system control valves from Danfos).
2nd option would be convert system to hydronic heat with mod con boiler, but it will be pretty expensive proposition.
@ April 26, 2012 10:32 PM in circulators burning out frequentlyif installer mounted cartridge type pumps vertically, and if there is spring loaded check valve on discharge, it traps air and can create situation with pump working with no flow.
@ April 22, 2012 7:18 PM in best high eff. gas boiler/ hot water heaterViessmann as a first choice, Slant Fin Bobcat with Combi Cat unit as a second (economy)
@ April 15, 2012 8:21 PM in Polaris used for radiant heating & domestic hot water.Steve , you are absolutely right in my opinion. Also i think plate heat exchanger is needed not for heating, but for domestic hot water. slant fin combi cat is just right for the job. Has build in circulator, activated by DHW flow sensor.
@ April 14, 2012 9:57 PM in gas line size? and how to determine size.help tim plzYes, i was referring to the original post.
@ April 14, 2012 9:54 PM in gas line size? and how to determine size.help tim plzIn NYC utility can run service to house and install house gas valve. this is where their jurisdiction ends.
@ April 14, 2012 2:56 PM in Not always mod/conTo do proper comparison, heating degree day method will be more accurate