Joined on November 23, 2012
Last Post on July 31, 2014
@ March 20, 2013 9:29 PM in Just Don't Get Modcon Boiler Pump Charts!Purging, If you shut every valve in the system except for the feed and the return valve of the loop your purging you get the air out.
@ March 20, 2013 9:20 PM in Just Don't Get Modcon Boiler Pump Charts!Prevent the air from coming out either of the two air vents?
@ March 14, 2013 12:02 AM in How do you clean a sooted gas boiler with water?Like a good idea and a lot less messy then mine.
@ March 11, 2013 2:11 PM in Flame impingementYour slower then I am and I'm at dead stop.
@ March 11, 2013 2:09 PM in How do you clean a sooted gas boiler with water?Burners and cover the electrics with a plastic bag and go to town. Ans away go troubles down the drain.
@ March 11, 2013 2:03 PM in new boiler. new construction. anyone ever have this? flame rolling outUsed soot spray with good results. RE michels has it.
@ March 11, 2013 2:00 PM in new boiler. new construction. anyone ever have this? flame rolling outIs a long time in a dirty atmosphere. Most manufactures state not to run equipment during construction.
@ March 10, 2013 11:28 PM in Vacation Home Heat Pump setting when awayA beach house with a 2 ton heat pump. Installed also I think in 1999. We are away as long as 3 months at a time. I keep mine set at 42*F. We have outdoor senser so the electric heat won't run unless it's below 30*F. The only problem is it takes a good long while to heat the place back up and I bypass my outdoor senser when we go down in the winter untill the house is up to temp. But hey thats what bars are for. Electric bill for the time when we are away for a few months normally around $30.00 $40.00 bucks. Now my HP is a hi eff. with both indoor and outdoor TXV. The only thing I have done to that unit was change a run cap last summer.
@ March 10, 2013 11:17 PM in Water heater out of warranty?!Is what it is. If its 6 years its 6 years, power or no power. I would call the factory or go over the counter guys head. If that fails tell the customer that the manufacturer has refused to honor their warranty and call the customer service line or local consumer affairs guy. This kinda stuff burns me up. We have no control over how the customer uses his equipment.
@ March 10, 2013 11:05 PM in Stupid call backs...That top of the stairs switch call many times. I tell the customer that a small problem is better then a big problem like a gas valve or a blower motor and that normally calms them down. And of course there's always the little old lady who wants a programmable thermostat because they save energy and she wants to do her part to help out and one week later she wants her old round Honeywell back.
@ March 9, 2013 4:10 PM in Looking for feedbackAnd higher efficiency get the government the hell out of the picture. They have already needlessly doubled the cost of a standard water heater with the stupid air baffle design. Now most areas are requiring a extrol tank, add another couple hundred dollars. We are supposed to be in the year I think that only 90% furnaces were to be allowed to be produced but that was thankfully pushed back. People can flat not afford higher efficieant equipment, if they could it would be we would sell. I just read a post from a lady who was having a hard time coming up with $600.00 just to repair her furnace. And don.t get me started on the cost of R-22.
@ March 9, 2013 11:05 AM in Control Module Replacement Compatibility QuestionA bad pump. Hard to belive no zone valves open.
@ March 8, 2013 4:11 PM in Control Module Replacement Compatibility QuestionMy friend are good to go.
@ March 8, 2013 4:09 PM in do u know what this is?Finned tube coil,.air would blow over the solar loop and then transfer heat to the other loop for what., Why not just use a tank?
@ March 8, 2013 11:29 AM in do u know what this is?A big two circuit coil.I can't figure out what heat he would be recovering from the water and doing what with it. Not like outside air in and inside air out heat exchange. Also there is only one set of pipes going to the coil. I think its just a big ole chilled water coil.
@ March 8, 2013 11:16 AM in Control Module Replacement Compatibility QuestionOn your existing pump the electrics are listed voltage, cycles, and AMPS if your pump is lower then 1.7 which I think is what a 007 is rated your ok. Anybody know for sure the 007 amp draw?
@ March 3, 2013 11:01 PM in Adding 410Just like you would R22 except with 410 it has to go in as a liquid as it is a blend of chemicals. Add it to the low side with the unit running and for sure weigh it in if for no others reason then to know how much you put in. It seems to want too fly out of the tank.
@ March 3, 2013 10:42 PM in How water boiler systemOf pump is on the boiler? If it has a speed selector set it on the lowest speed. It it doesn't and you have a shut of valve on the outlet of the pump or anywhere after the pump not before it throttle it down until you get at least a 20* f delta t. In other words supply water 190*f return water 170*f.
@ March 3, 2013 10:27 PM in PLEASE HELP!!!Most likely a bronze sleeve bearing. If the bearing still fits on the shaft and the shaft is not torn up clean off the oil and goop as best you can. Try any thing you can use, tape, Popsicle sticks, cardboard anything too fill the gap that the rubber cushion took up. Since it's the side opposite the motor you only need to keep the bearing from moving.Doesn't have to be even. Jam something on the bottom only or top only if you have to. Then add a few drops of oil to the shaft only. If you can keep It going till its gets warmer pull the whole blower assembly out and take it to machine shop and have them put it all back right. Don't see how your gonna ruin the motor but you may very well tear up the wheel.
@ March 3, 2013 10:10 PM in damper open for summer ops?Worry about it. May 2% loss of eff.