Joined on November 23, 2012
Last Post on March 9, 2014
@ February 18, 2013 7:08 PM in Intermitted gas furnance problemFurnace has a molded plug on the blower compartment shelf you can try cutting that out and wire nutting the wires togeather. Sounds like you have replaced everthing but the wiring harness.
@ February 18, 2013 7:02 PM in bryant gas furnace, no heat..Just don't know why I can't get it my own self. Went to lit. then prod data put in 350 and only mva's come up.
@ February 18, 2013 6:56 PM in bryant gas furnace, no heat..And still will only show me 350mva's
@ February 18, 2013 6:49 PM in Steam Pipe Coils and Sprinkler HeadsYou should pose that question of what temp to go up too to the Fire Marshal. Also I think thats the first time I used the word to or too more then two times in a sentence.
@ February 18, 2013 6:42 PM in What should the proper fpm velocity be for a furnace in aYour at less then .05 SP you should be able to go up to 900 fpm with no real noise.
@ February 18, 2013 6:37 PM in bryant gas furnace, no heat..Didn't see and Bryant 350aav. There is a 350mav which is a 90%er. Sounds like you need and inducer motor or a circuit board.
@ February 18, 2013 6:32 PM in bryant gas furnace, no heat..That furnace should have a two diget code. The first number determined by the short flashes and the second number by the long flashes. So one long flash followed by 3 short flashes = error code 13
@ February 18, 2013 6:27 PM in A math problem :)The only sensible thing too do with a water thats not working well is replace it.
@ February 3, 2013 8:41 PM in Triangle tube prestige mod con?I would primary secondary that for sure.
@ January 26, 2013 5:36 PM in Zone short cycles and t stat reads lower than settingThe heat anticipater setting on the tstat.
@ January 22, 2013 6:01 PM in Munchkin boiler 925 controlOne swirl plate and when I check the flue piping it look like the stubbed both air in and flue out and used a saw-zal to cut them both off same length. Also that plate is pricey.
@ January 22, 2013 3:04 PM in southern pride smokerHave Tim. I used to do a lot of work for Red Hot & Blue. Not tring to give offense or anything but the issue is the pilot. Also those smokers are design to have the gases blown around inside the oven and I'm not sure how that would effect combustion readings.
@ January 22, 2013 9:26 AM in Pigtail & vaporstatTo me. I shake like a leaf when I pull them out of boilers to clean for fear of breaking them.
@ January 22, 2013 9:23 AM in Banging pipesSo you have two circs, one for the boiler and another for the heating loop.
@ January 21, 2013 8:56 PM in southern pride smokerYou would do a combustion test when you have a gas and wood fire?
@ January 21, 2013 7:24 PM in Banging pipesBypass on the system? How is the boiler piped? Primary secondary? What happens if only one zone calls.
@ January 21, 2013 12:32 AM in southern pride smokerAlso want to blow some nitrogen through the pilot tube to clean that out. Then your done.
@ January 21, 2013 12:30 AM in southern pride smokerCombustion test. Clean the flame sensor and your done.