Joined on November 23, 2012
Last Post on March 21, 2014
@ February 22, 2014 5:05 PM in Tim; New IFGC QuestionSource was my Lennox distributor. They have basically stopped stocking the kits. I'm in the Washington DC area and I contacted my local code enforcement [WSSC] and was told they kits are only allowed on interior chimneys. I have used them on all chimneys in the past. I have a customer who refuses to believe me when I tell her she has to line her chimney. She says she hasn't heard of that. I ask her what codes she has heard of and she didn't have a answer for that, but still doesn't believe me.My local enforcers say it is new and went into effect on Nov. !st last year.
@ February 22, 2014 9:28 AM in Hydronic Air Handler in A Condo IssuesSister to ask her neighbors who they use.
@ February 22, 2014 9:13 AM in Tim; New IFGC QuestionIFGC on chimney friendly kits. Anybody have a copy of those sections. I'm told they are no longer acceptable on exterior chimneys
@ February 21, 2014 5:36 PM in Old p-tekHas a Embassy Weather Twin.
@ February 21, 2014 5:08 PM in New Nov.1st 2013IFGC on chimney friendly kits. Anybody have a copy of those sections. I'm told they are no longer acceptable on exterior chimneys.
@ February 21, 2014 5:05 PM in Soundproofing a boiler roomOf noise? What kind of boiler. I installed a Buderus atmospheric last week and found it to be nice and quite.
@ February 19, 2014 9:38 PM in Hydronic Air Handler in A Condo IssuesFan speed should lower the discharge temp which should make for a longer run cycle. I guess I would start by lowering the fan speed and that should quite the unit down
@ February 19, 2014 9:23 PM in Alpine Gas Boiler Venting ProblemBlue flame? Never seen a blue flame on a oil burner.
@ February 16, 2014 5:32 PM in Automatic vent dampenerWith tinman. Most of those dampers have 5 wires. Ground, 24v open and 24v close. The other two are the wires you need to jumper. Look at the motor and eliminate the ones going to the motor and the other two are what you want. But as you know be sure it all goes off when you shut it down at the stat.
@ February 11, 2014 8:09 PM in Condenser changeWas probably stuck some where. Why was the unit changed out? Was it a leaker was the system full of moisture? Maybe some crud in the piston and it shot into the coil. If it ain't broke now forget about it.
@ February 10, 2014 11:37 PM in NTI Ti100Maybe? But why is it only firing for 4 mins? Try shuting off the main power supply for about 10 mins and restarting. If that dosen't work call NTI.
@ February 10, 2014 11:30 PM in Laars low water flow boarda senser conected to the board? Maybe it needs to be cleaned.
@ February 7, 2014 9:16 PM in NORA is back!!!!I certainly don't want kids chained to sewing machines any more. I also don't like the fact the water heaters almost tripled in price due to gov. regs. Or the fact that dish washer don't get dishes clean any more because of gov. regs. Let consumers decide what features they want on their home appliances.
@ February 7, 2014 9:10 PM in New Inducers NeededThe motor only. You want the whole inducer assembly. The lennox book that came with your furnace may have a complete parts break down in it. It is next to imposable to get the inducer wheel off the old motor.
@ February 6, 2014 7:11 PM in NORA is back!!!!Is a heating fourm and not a political one BUT, The goverment has no business in our business. Unless of course your willing to hand it over to them. And Tim if the oil co. go under because they waited for a hand out from tax payers thats their fault.
@ February 5, 2014 9:05 AM in York heat pump/auxilliary element heatPretty much covered it. But the answer as to when to turn off the heat pump is never or, when its not working at all.
@ February 5, 2014 8:56 AM in NORA is back!!!!If the oil company's and manufactures want to spend their money for research let them do it. Why should the consumer pay for it.
@ February 4, 2014 11:24 PM in In wall baseboard heater making poping, clicking and banging sound.Be able to remove the cover and do some snooping around right at the heater with out tearing up the walls.
@ February 4, 2014 11:13 PM in Steam Rad not heatingI was just gonna leave that rad. off for a few days and if all was well replace that other trap.
@ February 4, 2014 7:11 PM in help with united technologies 1018If I touch the next one I put in and it fails will you replace it?
@ February 4, 2014 7:05 PM in Condensing Furnace questionsFrom the modulating. Only slightly more eff. and way mare costly. Also at least with The Carrier brand and I'm sure most other brands work the same way. You can't actually read the input signal to the valve, your meter will just jump around and that means you have a signal to the valve or that it and the board are talking. No meter jump and they aren't talking. Unless of course you go to the truck an get your oscilloscope