Joined on November 23, 2012
Last Post on July 31, 2014
@ February 6, 2014 7:11 PM in NORA is back!!!!Is a heating fourm and not a political one BUT, The goverment has no business in our business. Unless of course your willing to hand it over to them. And Tim if the oil co. go under because they waited for a hand out from tax payers thats their fault.
@ February 5, 2014 9:05 AM in York heat pump/auxilliary element heatPretty much covered it. But the answer as to when to turn off the heat pump is never or, when its not working at all.
@ February 5, 2014 8:56 AM in NORA is back!!!!If the oil company's and manufactures want to spend their money for research let them do it. Why should the consumer pay for it.
@ February 4, 2014 11:24 PM in In wall baseboard heater making poping, clicking and banging sound.Be able to remove the cover and do some snooping around right at the heater with out tearing up the walls.
@ February 4, 2014 11:13 PM in Steam Rad not heatingI was just gonna leave that rad. off for a few days and if all was well replace that other trap.
@ February 4, 2014 7:11 PM in help with united technologies 1018If I touch the next one I put in and it fails will you replace it?
@ February 4, 2014 7:05 PM in Condensing Furnace questionsFrom the modulating. Only slightly more eff. and way mare costly. Also at least with The Carrier brand and I'm sure most other brands work the same way. You can't actually read the input signal to the valve, your meter will just jump around and that means you have a signal to the valve or that it and the board are talking. No meter jump and they aren't talking. Unless of course you go to the truck an get your oscilloscope
@ February 4, 2014 6:36 PM in Steam Rad not heatingGot a call today for a large steam radiator that was not heating and another contractor had just installed a new thermostatic trap. I got there and drained about 10 gallons of water out of the rad. and pulled off the brand new trap and found it was fine. Then there was about 2 mins of gurgling and water started flowing out of the return water line. It did that on and off about every 3 to 5 mins. This rad appears to be on a tier with two other wall mounted rads. One at the entrance way the next higher up on a wall at the top of the first stair case and then the rad I'm serving at the highest point of the tier in an office. The lowest rad on the tier had a cold return line and the second one had a hot return line. I suspect that the trap on that rad is leaking some steam by that is going up the return line and into by top floor rad. I shut off that supply and my top floor rad started heating. Any other ideas on what could cause water to flow up the return line in case the phone rings tomorrow
@ January 27, 2014 3:16 PM in Gas Wall Heater Turning On and OffThe furnace turns on [ignites]and then off and restarts. Are the burners going on and off or just the blower? The soot is a very bad thing. A properly operating burner will not make soot. I would keep it off untill some one takes another look at it.
@ January 22, 2014 12:33 AM in New furnace but cold on 2nd floorNot have the correct speed settings on the fan. Most are set with dip switches and the default settings are normally for the max air flows.
@ January 22, 2014 12:29 AM in Bryant 987Fifty steps in Bryants service book for trouble shooting error code 41. Blower failed to reach 250 rpm or failed to communicate in 30 seconds. My guess is you have a "Failure to communicate" as they say in the movie. The service gude says to replace the Modual and motor togeather in all instances not one or the other. looking over the guide the service tech would need at least 3 hours to perform a proper check of that motor and need special equipment.
@ January 21, 2014 8:50 AM in Issues with & Replacement of Honeywell L8148E AquastatEvery post but no you do not have to drain the boiler to replace the control. You may try using a plastic wire tie through the loop of the jumper wire on the plug to add some tension that will hold the plug down and that will usually work until you get a replacement control. I would also contact Honeywell customer service and let them know your issues with their controls.
@ January 21, 2014 12:10 AM in Weil-McLain GV-4 OverheatingSays 8:20 circ stops 16:00 circ comes back on.
@ January 21, 2014 12:04 AM in Drain boiler to replace boiler drain?It's pouring out the stem just wait unitill the cold weather passes. But you wont crack the boiler by draining it, swaping out the BD and then you can let system water back into the boiler and bleed the rads.
@ January 20, 2014 7:16 PM in Wifi thermostat for 20 zone radiant floor systemPrices here but thats gonna be a lot.
@ January 20, 2014 7:02 PM in Very Unusual Honeywell Zone Valve TroubleThat once you open it manually it stays open? If so you may not have a big enough transformer to power open all the zones which would account for the randomness of the issue.
@ January 20, 2014 6:23 PM in Weil-McLain GV-4 OverheatingAn old one. Probably a stuck bypass valve. But did you find out why the pump stopped?
@ January 16, 2014 3:47 PM in Water hammer noise after new gas boiler installed007 or bigger. It looks bigger.
@ January 16, 2014 3:33 PM in Baseboard Heat QuestionA model 2408 on a search. Sounds like a safty limit may be opening.