Joined on November 23, 2012
Last Post on March 5, 2014
@ January 16, 2014 3:47 PM in Water hammer noise after new gas boiler installed007 or bigger. It looks bigger.
@ January 16, 2014 3:33 PM in Baseboard Heat QuestionA model 2408 on a search. Sounds like a safty limit may be opening.
@ January 15, 2014 8:31 AM in PART 2 THE BEST IS YET TO COMEChuck knew that if your gonna drink all day you gotta start early.
@ January 15, 2014 8:22 AM in Dumb furnace questionJump "R" "G" to get constant fan operation.
@ January 13, 2014 10:36 PM in Wiring Lochinvar Knight + single Grundfos AlphaMuch about the Knight but would highly recommend P/S and a buffer tank. Also leave the plug on the pump and wire a receptacle to the boiler.
@ January 13, 2014 10:26 PM in Been sitting here pondering where the last 40 yearsThe Champion heat pump and the bic lighter shaped thing you stuck in the defrost board to by pass the time delays.
@ January 12, 2014 11:48 PM in Why not a zone for every room?Some thing that is easy to do if you do it from the start. Trying to do it after the house is built requires a big repipe. As far as matching the small bedroom load to the boiler you have to install abuffer tank.
@ January 12, 2014 11:34 PM in The irriating questions i just dont know!!! but i should!About the money. less wiring in the furnace.
@ January 12, 2014 11:27 PM in "Normal" pressure and temp?Is way to high. Turn it off and call somebody.to check it out. And stay away from the relief valve.
@ January 12, 2014 11:19 PM in Furnace downfired itselfTo force all the heat either up or down.
@ January 10, 2014 9:04 PM in Viessmann Vitodens 200 or Triangle tube prestige soloAbout the TT being oversized add a buffer tank.
@ January 9, 2014 8:33 AM in How do i get this downWould you get rid of that? Seriously I would first call in a asbestos Co. and have it tested. I had an old boiler that had asbestos around it and the co. came in and wrapped it up in plastic and had I'm not kidding, 10 guys carry it out in one piece.
@ January 8, 2014 11:25 PM in Viessmann Vitodens 200 or Triangle tube prestige soloGo with the TT 110 especially if your adding the indirect.
@ January 8, 2014 11:15 PM in Honeywell "Smart Valve"- SV9541- test procedure to confirm it's bad?You get a atta boy.
@ January 7, 2014 10:05 AM in 90% furnacesBut my guess is it's just a vent line and not sensing pressure. Carrier is using the same valve on there 80% & 90% single stage and the instructions say on the 80% that the tapping for the hose does not need to be sealed.
@ January 7, 2014 9:58 AM in prolem with lennox pulse furnaceBut are you sure that the air flapper is installed faceing the right way. I only ask because the directions that come with the kit talk about the "kidney shaped holes" faceing one way or the other and I saw nothing that resembeled a kidney on that air flapper. So after several no light offs I turned it around and it worked just fine.
@ January 4, 2014 7:55 PM in UPC TG9S FurnaceYour vent system. Will it run with the air in pipe removed. Will it run with the vent pipe removed. If it runs with one or the other pipe removed check that pipe for crude in the pipe., Are you recirculating vent gas into you air in pipe?. Some of those furnaces had a restricter plate on the outlet of the secondary if it's deteriorated you may be recycling combustion gas.