Joined on November 23, 2012
Last Post on March 21, 2014
@ April 20, 2013 12:03 PM in Direct Pump TT Solo 110 with 3 zonesDirect pump that boiler with that piping design. You must primary secondary.
@ April 14, 2013 10:54 PM in subcoolA bad TEV not letting refrig through and causing refig to back up into condenser.
@ April 14, 2013 10:50 PM in vacuumTo evacuate a system is after all the holes are filled and there are no more leaks. Rim shot boom. Take my wife, please take my wife. Or as Tech says after all the mositure is gone or in his case the flood has subsided.
@ April 11, 2013 7:51 AM in Never Cleaned Munchkin 80Mservice tech in your house again. Like the others said it takes less then 15 mins to actually look at the HX. And maybe and hour to clean. I have open up Munchkins after many many years only to find a nice claen HX.
@ April 9, 2013 8:18 AM in More efficient water heater.the rest of the year off and invent away to get my wife to stop nagging me.
@ April 9, 2013 8:10 AM in Indirect installation on Alpine with MCBA controlAnd my brains not fully awake yet but as far as questions 1 & 2 go I would use the piping off the manual that came with your boiler and not the "new manual". Question 3, you want only one pump running so your recovery time on the indirect is as short as possible.
@ April 7, 2013 1:29 PM in radiator use as A/C?No condensation then there is really no cooling.If you can't lower the dew point whats the point? On the other hand if you take a beer out of the frig and set it on the table and you get no condensate on it you shouldnt need the cooling.
@ April 7, 2013 1:18 PM in rheem warm air furnaceAdjustment that has a 2mm set screw inside a 3mm set screw? If it is you need to replace the valve and If you ever find the guy that dreamed that up, kick him in the butt.
@ April 7, 2013 1:10 PM in warminMaineInfo please. What did you clean. Did you open the oil filter. Did you remove the nozzel?
@ April 5, 2013 10:26 PM in Thermostat C wire to "COM" on Taco SR502?Check between that "com" and the "T" terminals. If you get 24v you should be ok. But for some reason I don't think that top left terminal strip is and output.
@ April 5, 2013 8:59 AM in Pumping Awa QuestionI use those evil on off tstats and they stay within a 2* diff. Thats fine for me. Also when it's broke it dosent take hours and hours to trouble shoot and cost a thigh and a shoulder to fix. I have found even the most simple energy saving devices don't save enough over their lives to pay for the replacement costs.
@ April 5, 2013 8:39 AM in Stupid question here but can't seem to figure this out.First of all it’s a 40 + year old boiler is any time spent repairing and not replacing is a waste. But if the customer insists then I would first make sure he’s gonna pay regardless of results. Then I would start by disconnecting aqua stat and cooling down boiler and starting top floor zone only. Let boiler fire up to maybe 160* and see what happens in the other 2 zones. If other zones are fine most likely aqua stat if not you might be able to check by feel whats up with the other zones.
@ April 4, 2013 6:20 PM in What are the flow rates coming out of this Tee?What goes into a tee must come out rule applies here. So 3.
@ April 4, 2013 8:42 AM in Digital thermostat on an incremetal PTAC (type K) with electromechanical contorl boxWho/s gonna push the buttons and where are you gonna cram all the relays needed? You have to order the PTAC's for wall mount tstats if thats what you want to use. Sounds cheep to me for the whole new controller board. Any other way is a can of worms.
@ April 1, 2013 4:30 PM in Munchkin burner making steady loud noiseA bad blower. If you can't find a power switch at the boiler it will soon enough lock up and stop.
@ April 1, 2013 4:25 PM in Window AC water slinger vs dry questionBeing is that it's not measurable due to the fact that there are times when the water is in the pan and times when there is not. Same with that A/C unit. I used to always fill those drain pans up after replacing a 9watt cond motor to get the box to pull down. I love arguing hypotheticals.
@ April 1, 2013 4:11 PM in Need Help With Honeywell RelayLike the relay in Pauls first post go to a local supply house and ask for a 90-340 relay or just bring the old one in. Make sure you have the retaining wire that keeps the relay in place.
@ March 31, 2013 4:41 PM in Sandy Boiler Replacements and the Sooting Phenomenon???Has a blurb in their installation instructions that says the furnace can be used for heating in a house under cost. "providing clean outside air is used for combustion"
.they specifically list "drywall dust" as causing "fouling and plugging of furnace components."
@ March 31, 2013 2:34 PM in Pump for Washing machineFix is to move the washer up where the drain is. That will also make the little women happy since she won't have to keep draging the clothes up and down the stairs. Bring the dryer up as well.
@ March 31, 2013 2:29 PM in Happy EasterMay you all have a happy Easter as well. The pork shoulders have been on the grill since 9 am